Type: Posts; User: tinner73
what color is the room painted?
not many of the old timers here anymore.
don't insult the southern states like that...thank you very much.
so long a$$hole.:CU:
you are correct..it is a big word. that you can't spell.:whistle:
you weren't even close.:angel:
little help please.
looking for the birth date of this dinosaur
carrier serial #5091a02098...........i'm guessing 50th week of 91.
ill be even more impressed if you tell me your return air temp is 72.3 degrees.
post a pic.
pull those return grilles and see if the noise goes away.
i am unfamiliar with that particular fan coil but the blower needs to match the condenser tonnage. it could be set for 2000 cfm (5tons)..you need 1600 cfm.
i would have put that on a heavy gauge plenum box with 1" lining for sound.
not sure what can be done now that it's on a stand. maybe they can skin the stand with 1" insulated...
what kind of noise?
get some ear plugs in the interim.
i wouldn't run it without a filter.
make sure you have a low restriction filter... merv 7-8.
search out Baldloonie on this board.
he's in your area and one of the smartest guys around here. his company does fantastic work.
easier to tell what you need when i can see what you have.
Schaumburg..2 man operation..neither of us are pushy salesmen.
email is in my profile if you like.
i'm local if you'd like a quote.
replace duct work with the proper size.
you misunderstood me.
i wouldn't put anymore money into a system that old. time to get a new one.
depending on how much you need...yes. have them find and fix the leak first. fix it now it will not get any better.
flex duct in a crawlspace only invites critters to live inside the duct.
1.) fill out your profile. maybe somebody on the board can help you.
2.) put $0 into a 24 year old set up. you got your $$$$ worth out of it.
why would you want to do that?
are all of your returns and supply registers open?
iced evap is caused by lack of airflow or lack of refrigerant. you have one or the other.