Type: Posts; User: bob1420
was ice in bin loose or big ball of ice ????????????????
check at action sales in city of industry and yes need to be nsf
yes do it all the time 6and1 not control driver
when you remove coil insert screwdriver in to coil secure it so it wont fall out or remove a leg of power to it
6 to 8 month old hoshi km 600 mah on ice o matic bin 3 filters, pre carbon , phosphate, cust calls black stuff in ice oped it up worst ive seen in years dark green/black slime everywhere ,clean...
try ice machine sales in commerce california he was dealer for many years
you may call ice machine sales in commerce California they were dealers for years Tracy the owner good guy
same prob at assist live no air gap between freezer wall and bldg wall same with floor also found fire sprinkler above box leaking 25+old quoted new box only solution
suction during harvest way too low should be up around 100 block off condenser and see, over the years have put many fan controls on roof with no problems
message sent thanks
i agree 3 weeks 20 hrs cant pay bills on that, 6 guys also i make alot more than other guys so no pm's for me just no service calls,dont want to go somewhere else and be the new guy may not have a...
any info helpfull thinking of applying there thanks:grin2: the company ive been with 20yrs way too slow
you need to put guages on to see press
bad suction line thermister
check the cube size control if ice too thin will cause both error codes
work on these all the time never seen a llsv on this model and true started useing herm comps to keep cost down
stop evap fans and if coil temp control pull from coil or jump stat ,cap tube not on suct line would not account for 25f add gas till frost 1 foot from comp,works everytime,cooler or freezer, on...
harvest is term by thermister on suction line,need more info, you can blow into float vent to emty and make machine go into harvest,what are your press on suct side,good fresh water flow needed to...
used very good condition true t23 cooler located in haciendia heights ca,750.00 OBO call 562-712-3692 for more info thanks bob
late call at hospital comp short cycle on cab thermister,box 40 inteletraul showing-05,pull sensor and unit runs fine ,show86 on display now,will unit auto defrost over weekend with sensor out till...
lots of lookers
been with current co 17 years looking to make a move,:cheers: very strong refrig,ice machines,glycol chillers,a/c,own tools,good drive record,will work all hours,pay up for discussion. ...
on cap tube i shut evap fans off charge till frost 1 foot from comp works every time
inlet water valve leaking ?
had one a month ago short in lh door heater cut wire no more problems cust declined new door