Type: Posts; User: El Presidente
August posters, check your mail. Anyone else, let me know.
Version I have is 6.201. Not sure if that is even current anymore. Haven't used it since 2011. Who wants it?!
You're welcome! Let me know if you need anything else.
They work. I would take the BACnet over Lon. More functionality, more capacity, and less issues. They are both monitoring and control. You can see the points lists here:
What do you want to know?
You should see just a bunch of points. The number after the object name corresponds with the address in the stat. For example StartStopCommand_000 corresponds with group address 1-00. 001 is 1-01...
What gateway firmware version? If it is 1.x you just have to have the equipment connected to see the points. If it is 2.x you must go in through the webserver and perform a discovery within the...
Graphical programming is available.
For Daikin you have to limit the writes for changes of value. If you write On when the unit is already on every two seconds it is fine as the gateway will not actively write to the indoor unit EEPROM...
BACnet - Excellent, this got all my points working except for MSI, MSO, MSV. Thanks!
Xarralu - SCL Elements confirmed Multi-states will not be available until November Firmware update.
I'm trying to use this controller to run simulations and trend points on my VRF system through a BACnet gateway.
Script syntax for the request is (device instance, object type and...
I'm trying to help out a guy integrating Tridium and LG and he says for SNVT nvoUnitStatus, his system reports “Type Size Mismatch (13bytes). LonMark says this data type (hvac_status) should be 12...
Ok, thanks anyway.
I'm trying to help out a guy integrating Tridium and LG and he says for SNVT nvoUnitStatus, his system reports “Type Size Mismatch (13bytes). LonMark says this data type...
What was the problem and how did you solve it?
Have each of the indoor units been assigned a group address? If not, do that and then cycle power on the gateway.
C, check your mail.
threefiddy, my e-mail bounced back. Not sure what the problem is.
C, add an email to your profile.
threefiddy, check your mail.
Ok, what's the IP address of the Jace? It will have to be 192.168.0.X if the gateway is left at default IP of 192.168.0.1 without enabling the gateway as a foreign device.
If it is on a different...
De nada and you're welcome.
amigo, check your mail.
What IPs for the jace and the gateway? I'll send you the setup tool.
Can you ping the gateway but not discover points? Are you on a different subnet than the gateway? If so the gateway might have to be setup as a foreign device.