Type: Posts; User: jmo90280
so here's an update replaced the board and condenser fan motor and unit is working fine now
Dolly?.....toss it to the corner or the roof n call it a day...lol j/k
the liquid line runs through the interior panel so the condenser is probably dirty ..ok now i know why that wall really heated up I checked condenser fan not stuck and windings ohmed out will...
[QUOTE=jim147;13655221]IIRC that unit has a yoder loop between the doors to keep moisture down.
Yes I found out that the tube runs along the interior walls so that explains that and yes it uses a...
Yes it is strange that the wall would get so hot, i was thinking that it might have been the ice maker too since it is the only thing close to that wall but they told me that it hasn't worked in...
Hello, so my cousin asked me to take a look at his Samsung RS2630sh side by side after he noticed that the wall that separates the freezer and the cooler was extremely hot then he noticed that the...
Hello I'm just wondering If anyone has ever charged an R22 system by adding 35 to ambient temp and then us that number as the saturated temp and converts it to pressure...JUST WONDERING
Give the guy a break hes just rusty, I didn't start working in the field until a couple years after I graduated at first I too did not remember many things I was taught.......and after a few year I...
Replace the oil in the compressor purge the evap and condenser replace LLFD and pull a good vacuum
Don't forget the transformers
I work on a lot of bards also mostly for cell sites , common problem is wrong gauge wiring from the manufacture
well I graduated from high school and didn't really want to go to a 4 year college so i enrolled at a trade school hvac caught my attention and i stuck to it.finished the course couldn't get a job do...
[QUOTE=hvaclover;13361361]Yeah, and at 30"HG on your lo-side gauge you have how many microns? 25,000, and the mfg says as low as 200 microns?
29.916"hg = 100micron
Good to hear good things about this scale because i just bought one lol
yea I do like it but I prefer charging by the "split":grin2:
LOL just tring to keep u on your toes jp:whistle:
Has anyone ever used this scale?
You don't need a micron gauge to know your pulling a good vac your gauges also tell you, just make sure you change the oil in your pump after every use
sounds like a restriction probably the drier
Replaced the cap tube and drier , system is working like a champ.:grin2:
Thanks 4 the replys:cheers:
I know theres alot to consider (light,windows, ect) but in general what would u use?
I get some of those too but i collect after for the same reason (customer satisfaction)
I put the oil back in through the discharge right?