Type: Posts; User: cmakowk
Search took 0.02 seconds.
Yes...that is another thing.
Usually if it is that far off then maybe
it is setup as platinum and not nickel.
I would still check the calibration table and change the AIs back to factory...
Are you trying to maintain discharge air/ mixed air?
Do you have a preheat valve?
Might just be able to adjust the PID loop...
Follow the procedure pare provided, verify the readings are the same
as the factory readings on the sticker on the back on the DX
then calibrate accordingly...
The mixed air temp should not have anything to do with a relief damper...
Maybe you're talking about the OA damper?
If you truely talking about relief damper then it has to be
I have a Trane Summit ver.17
that has Comm3 and Comm5 devices.
Comm 3 devices are reading fine.
The Comm5 devices are lon and were reading except
for a lon fieldserver, which translated AAon...
How do I check the LGR or modify it
to make sure it is translating?
Its CCN trunk going to a LGR...I need to verify that LGR is setup correctly.
I have a couple Carrier chillers daisy chained
to a Automated logic LGR.
How can I connect to this LGR to verfiy proper
communication and if it even reading the points
So Jaces are used with I/O modules.
What protocol are they?
Are the Jaces setup for whatever protocol you program them for?
I am trying to figure out if we can use a ALL Tridium system
Thanks for all your replies...
I was referring to the Vykon controllers, which
you guys are saying is not Tridium but they are on Tridium's website.
So Tridium DOES NOT have fully programmable...
Using a Tridium front-end:
How many people use the tridium field controllers?
How many people uses Tridium front-end with different
manufacturer as field controllers?
Thanks for the response....
Just trying to get the pros and cons....
Does anyone have Delta literature?
Is line code the latest programming done for Delta controls?
Do they have some kind of Graphic programming?
Does Delta have a LON interface?
Page 45 on
Just an update...
Found no documentation but the relief valves are rated for 15 psi.
We installed local pressure controls for each boiler to modulate
low and hi fire at 12 psi.
I put the...
First, I would check to see if the graphic
has the correct AV99-AV100 mapped.
Open the graphic, go to edit, and double click on the setpoint
box to see if it is the correct controller and if it...
Does anyone have literature on programming Delta?
Can it be done from the workstation?
Need more info...
Are you adjusting setpoint from Head -end?
Your head-end is older or newer?
I will take a second check around and see if I can find anything.
Thanks for the replies...I will update you later!!!
It is two stage low/hi fire control.
Thanks for the replies...
I believe ctrlguy is correct when he says
the valves were undersized when installed, the current steam pressure is lower than design
The problem is on VERY cold days,...
We have 3 steam boilers that supply steam heat to certain places in the bldg.
Each boiler has pressure controls to switch from low to high fire.
The current steam header pressure setpoint on the...
What is the most efficient way to control steam boilers?
I have 3 steam boilers with a heat exchanger with
1/3 , 2/3, and a third modulating valve that was an old bypass
but was converted...
The internal status of a LonWorks device will be used to determine the offline/online status. To be set to online, the internal status of the device must be configured online. The Query Status...