Type: Posts; User: pecmsg
From the looks of the stain and rust its been doing that for a while. SH about 5*?
Learn to slow down. I get the impression you jump to quick.
“Problem was Short Cycling, Found LP control set for 0 & 20#’s” Without hooking up gauges how do you know this and how do you set...
Ritori New Guest
So what can cause the high limit to trip?
The indoor fan ramps down to a minimum during the off cycle. This is normal operation.
Thermo Bank was a well-designed system, I don’t think I would try and redesign it in the field.
What parts are you trying to replace?
Be prepaired for a drop in output 10% or more
My mistake yes you will be moving 15+% more refrigerant.
Don’t Do It
Looks like your loosing over 15% in capacity just on the compressors, maybe a little more by changing refrigerants. ...
Use a current sensing relay on the main blower
Welcome & good luck with the Training center.
God knows we need the trained manpower.
Papus Refrigeration still down there?
I see them inside the box behind the evap.
Something like this:
Market work will be one of the best educational experiences you’ll get.
You can always go back to oil
As you hand them the bill
Down load the apps from Emerson and Tecumseh, a ton of information that’s use full in the field.
I’ve seen my share of R-502 changed to R-22 changed to god knows what. Like you change to a...
Theres a ton of information on the web,
Variable Air Volume systems
Change the Cap tube and suction line as 1 unit. With a compressor I would plan the better part of a day.
Let me guess
Fresh out of school
We have ways of making you talk!
One beer or two?
A definite Possibility of a Maybe!
The outside area of this WI maintains 75°Fdb/50%RH how do we get 80 – 90%RH inside?
34*f and 80% RH
I’m glad I do refrigeration………………
That’s too much to learn!
What do you expect from 1 year of schooling?
Your question might get a better response here:
I don’t think the OP is talking a small generator!