Type: Posts; User: BasicCntrl
Search took 0.01 seconds.
Is the Main Disk Defined for the Insight Node (0)?
>Point, pRogram, Time, Message, Cancel, hArdware, Setup, Bye ?A
>Cabinet, Printernode, cAtegory, Disk, Modem, Hostcaller, Thisnode ?D
Breaking the statements apart puts it in laymen’s terms
and then you could even clear the trace bits to see what is really going on.
10 IF("PH.CHLR.LAG1.STATUS" .EQ. ON)THEN GOTO 30
Sounds Great –
Where is the Meat?
Post some examples of it
Smart Controls uses VisualControl Graphical Programming (SC-VCGP)
When I browse a device I get valid data for all my Network Variables - everything is fine. When browse the same device using its Functional Block, I get erroneous data in the browser...
Is there any remote chance your PPCL program is using OIP statements to enable and disable the TIU?
That’s what I use to do way back when I came across the TIU.
I would write PPCL to...
Andover’s programming language is known as “Plain English Programming”. PEP utilizes line code similar in structure to Siemens’s PPCL – only much more powerful. One of many ways to view,...
Perhaps try different baud rates?
Check settings in HyperTerminal (8 N 1)?
Try a different cable?
If Siemens is still giving you good response and service stay with Siemens only. Are you familiar with Lonworks? I have installed, programmed and used both Lonworks & Siemens...
I guess I must to reply to this thread since I used to work for both JCI & Siemens.
Just like “MDaily” said, you will find that JCI is micro managed. There are managers managing managers. JCI has...
I have an old Facilitator site with about 15 UNT110-1’s on its N2 running the Terminal Unit – Unit Vent applications.
Currently they have a PC running windows using HyperTerminal as the user...
BASIC is the key word here …
Thank you for the tip on Distech's version of the BASIC programming! This is just what I have been searching for. I knew there had to be an easier way to...
hum.. For a wireless thermostat, for both residential and commercial, ... If $$$$$ is no object get the whole system.
may wanta look into:
Let's not forget BCS.
Why deal with Data Mate when you can have BCS - assuming there happens to be an old computer lying around w/ Win98.
Thank You all for you input keepyoucool2003 & SCC -
I shall check these settings when I get back to the job site.
I am stuck with using the heat cool set points because they...
My HVACPRO displays the actual cooling \ heating set points at 145 \ 138 F.
They should be around 73 \ 70 F.
VAV Box - Temperature Setpoint
*ADF 13 Actual Cooling Setpt ...
Thank you - keepyoucool2003!
I am working (actually beating my head in) with HVAC PRO Version 8.07
I have successfully configured and started up a 1420 VMA as Single Duct with box reheat.
I also have an additional, non...
A dx9100 w\o tag names = reverse engineering – happens all the time.
You gotta play detective and work from the program out & hopefully there some input & output wires marked or tagged – this is...
I am not sure if this would even work...? But-
How about using TE-6700 series room sensors with the warm cool adjust?
Might (can) they work somehow with the DX-9100 AI's?
You might want to check the C:\WGX9100 “GX9100.EXE” Properties. Left click on the GX9100.EXE file select Properties –
Check the Compatibility mode to see if you are running Windows 95.
You need the famous JCI GX9100 programming tool and the DX Commissioning software for the DX-9100 controller. The programming tool has an option to download the date and time from the computer you...
Excellent Quote! I totally agree with you. I have had the pleasure, and a little pain, of working for and representing six different control companies and in the end it’s always the customer...
Be very, very careful.
You are dealing with rocket science!
When it comes to LonWorks, and making (simple) controller program modification(s) allow more than 3 times the amount of time it will...
The Cable Product # is: 540-143
9 pin female: RJ-11 connector:
3 ------------------- 5
2 ------------------- 6
5 ------------------- 1
5 ------------------- 2
Does CIS or Datamate exist? How do the airbalancers balance the TECs?
Yes, both Datamate & CIS exist.
CIS is the software the air balancer needs to have installed their laptop to field...
What you need to do is change COM1 to COM5 and then change COM4 to COM1.
Is this datamate the spin off of the famous BCS programmer w/o Editing capabilities?
It never hurts to create a System...
I am running the DMS Operator Interface V11.41 software using XP with no problems. Is this what you are looking for?
Try looking at the TCS Basys Controls. They offer internet access with a 2min update delay.