Type: Posts; User: 381engineer
I love using google voice in gmail along with a headset.
It apparently pics the port number automatically. I plugged into different ports and the port number changed each time.
That being said I was able to try again with a know good device.
Its the first device listed under Universal Serial Bus controllers.
Listed as CCN Converter
It also shows up under Ports
CCN Port (COM8)
Plug it in and the status light flashes about every two...
Yup, it's there.
Unfortunately I didn't think of trying on the other guys PC. (Duh...)
But it's looking like a bad adapter, Ive tried installing on other PC's with the same result which really sucks cause it was a...
I read that, pretty sure I followed exactly. Uninstalled re-installed a few times still no go.
I'll try again.
Does anyone know if the adapter will be recognized if not connected to the bus?
Just got a new service tool (V2.2) and installed on XP laptop. (part# 33CNNSTKIT-01)
Installed per instructions but get "Unable to Validate Product Key" when connecting to bus.
I tried another...
Oops... sorry about that.
Looks like Virginia 5P is a better rate.
How they come up with these rates is beyond me.
I just looked at the 5P rate and On Peak demand starts at 6am Oct-May.
The On Peak Off...
Can you access the interval data from the utility company? Are you Va Dominion Power (GS-3)?
if so you may be able to upload 18 months of interval data and just see when they are hitting the peak...
I have a question for you guys.
When using optimal start do you take into consideration the given utility rate schedule for the building?
What I've run into in Northern Virginia is that most...
Circon's Network/Visual Integrator has a LNS connections report plug-in. Works nice!
I think Lonmaker has something similar. Maybe Lonboy will chime in.
He is the Lonmaker guru.
Run SmartInstaller and you should be able to load anything you need.
Loytec now offers a full line of BacNet and Lon controllers and you can purchase direct.
The US office is in Wisconsin
Did you upload xif from device or do you have the xif/apb from manufacturer?
Sounds very similar to an issue a friend just had adding some Distech ECL 300's to a LM database when he just tried to...
You will need an LNS tools (IE lonmaker) to access the database.
If you can locate the database and then find the controller on the network that is missing I'd see about opening the device plug in...
Didn't think Tridium is an actual LNS management tool?
Be kind of expensive wouldn't it?
Give them a call if you have any questions
Catalyst is their graphical programming tool tool for the UHC400.
Check out the above link.
Highly recommend his class.
He takes care of his students.:cheers:
I highly recommend Circon Visual Integrator.
it is basically a network management tool packaged with a front end. You can however...
If I understand you correctly.
You may not see a read value until you write to it from the LVIS.
Add both the read and the write value to the selected control in the lvis project.
Data that is greyed out is not reliable, meaning there is a form of communication problem.
The L-VIS has a built in webserver where you can see all your data points and the status.
If you are...
I purchase direct from Loytec but you could contact CT supply also.
I became a big fan of the Loytec programmables when I tried the LIOB180 series, many different configurations to choose from, LCD display, extreamly powerful programming tool (GPL, Ladder, Text,...