Type: Posts; User: mor1mor1
...found the info........
Have a couple of questions
1. Do I connect Yellow from condensor to Y/Y2 also at furnace and
2. where do I connect other (BLUE) wire from condensor to the furnace ???
Thanks for the quick response.
The t-stata ta a RITETEMP 6030 touch screen, the furnace is CARRIER Performancs 80 Model # 58CTA and AC Condense is GOODMAN GSX130361.
Good day to all,
I'm trying hook up a thermostat to furnace and AC (split system)
The tstat terminal are ===C B O W2 W Y Y2 RH RC G A
the Furnace (Carrier) TERMINAL ===R, Y/Y2, WW1, COM24, G,...
This is “NEW INFO” From the research I’ve done indicated not to use rods with “PHOSPHORUS” when brazing copper to brass ????.
I’ve already brazed the other sections of copper with Harris...
Thanks for the tips. Seems like White paste flux, and 45% silver is the "method of choice"
Yes I'll be using nitrogen.
Good evening HVAC Guru's,
What is the best method to braze 7/8 and 3/8 HVAC copper line set to brass service valve. Any help will be welcome.
Thanks in advance