Type: Posts; User: maxscott
we going to break up the trunks in to several and run async out of clients to halp run faster the server being drug down ..
CFM sensor or static 2/3 down the trunk line single in
I know Siemens has problems sharing points a crossed a trunks. if you point are being totalized from trunk to trunk async services could be problem stop them and restart.
I have run in to a major problem with Siemens BACnet PXC Compacts I have been in hundreds of panels a year never had a problem until last week . After talking to a Siemens teck he could not confirm...
2020 vAV cooling only streaight duct
2021 vav cooling and heating switches from thermistor streaight duct
2022 VAV with Electric Reheat streaight duct
2023 VAV with Hot Water streaight...
2050 and 2051 are fan on all the time
the boxes have heat and cooling
we working with a BAPI wireless room temp 4 - 20 ma no luck trying to work it into a siemens system MEC
Apogee has two key colors Black and White letters are the actual address keys .The white keys are /2 example key 8 is really 2
Last time I worked on one I used hyperterminal and the MMI port.
SKD62U will do it
no just when you add to the pannel the addressing is lets say pannel 0 fln 1 point 1
MEC and a MBC are two different animals the thread asks about MEC out put module.
Which is a AO/AI or DO/DI like a 549-212, 549-214. But if you are asking about a MBC . The white keys are binary(...
there is a dip switch seting you have set address on it . and some have a seting for speed other are universal type( fln bln)
repiars some siemens parts check out web sight
Could be node 0 or any node defined to be the server or back up server
What Application? there is lots of them .
Run the port at 9600 not 38400 and it might help ..
Datamate still works just fine I have found some times you have to set the MMI port speed down to 9600 to use Datamate with the power MEC. I did here that some one hacked Advanced and no longer...