Type: Posts; User: mechinc
Search: Search took 0.01 seconds.
Anyone know of a temp/humidity/diff pressure combo sensor or meter
or panel available?
I have a operating room that I need to control all 3 conditions.
Microset II and MSTP
Looking to calibrate the humidity value.
It is 10% off.
I can take the AV-102 and put an offset in programming for control purposes but the display still reads wrong.
I have a Microset with Temp and Humidity display.
The temp is AI-0 to AV point but the humidity is straight to AV point.
How can I calibrate it so the display can show the
What are you talking about?
I have the Envision for Bactalk software...
Do you have your firewall enabled during install?
I do not have a copy of the original job.
If I rebuild all the displays in the BCM-ETH with Envision,
How do I pass those displays to the BCM -WEB?
I have a site with BCM-ETH with BCM-WEB but no workstation.
There are no backups but I need to modify the displays.
I have Envision for Bactalk 2.6 on my laptop so I can modify
the programming and...
Check out CDW...
Eaton Management Card Contact / RS232 Serial - remote management adapter
Mfg. Part: 66104 | CDW Part: 1780442 | UNSPSC: 43222633
You add this card to one of their small...
Teletrol “The Integrator” is the system used to connect to field controllers via RS232.
The Filed controllers are Teletrol TeleSys AX.
Anyone pulled this system back or converted to...
anyone with a driver or any news getting this driver?
The NCM by default syncs its time off the 60Hz power frequency. In this case, the job site had lost power several times and switched over to an emergency UPS which caused the time problems. ...
So it is a NCM that has a modem connected to it,
which is dialed-up by a workstation.
Are there any other workstations on the network?
What are device subnet and node IDs?
To change the...
We have both the NCM COAX card and the COAX/ETHER combo cards...
I seen some posts regarding flashing the MP581s...
Will this help or hurt?
How do I determine what version the controller is at
and what version I have?
It was an existing trunk and we added the 3rd party in the middle.
I performed the rebuild function and other MP581s installed but this one just won't. I will try to check trunk but it is funny that...
Yes, UI into the NAE and double-click the NAE.
Just Enable the Bacnet exposed.
Then reboot the NAE.
Then you should be able to discover the device instance
and change it to what you want.
We tried to unassign and save it.
Then clear RAM and Reset.
Then let the BCM discover.
Then tried to reassign.
The controller comm shows UP.
I am using a MP581 Summary graphic.
At first, the...
We added a 3rd party LON device to a tracer Summit
system using Rover and the workstation.
Now an existing MP581 shows Incomplete Bindings.
There is another MP581 right next to this one
Thanks...I will try and let you know.
I have a site that has a Alerton BTI with VLCs, older ViewPort, VLC1188C, and a few Niagara controllers on MSTP.
The bactalk workstation is running 2.6
I am getting a segmented not supported on...
Yes, I think using CPL is the only way to command bacnet/ip points.
When I use the property reference, it cannot use bacnet/ip points
because their property is not available.
I am trying to command bacnet /ip points through
Tracer Summit. I can read them but when I map
Output points then use the property reference
the propoerty reference is blank.
I can use the I/O...
Does anyone have info on FEC accumulator setup?
How about an example?
Trying to setup but only shows vague info on the prescale.
Make sure all Java is uninstalled.
Delete internet temp files.
Manually Install JRE 1.5.0_6
Disable Java update in console.
Reboot then try...
If it still gives same error then since it is...
Results 1 to 25 of 225