Type: Posts; User: MwTechInc
Search took 0.02 seconds.
If, as you say, all 4 ovens have been trouble, then its probably not the ovens.
You didn't mention if when you changed parts the oven(s) worked for a given time.
LP or nat?
Line sizes, main...
Thanks good link, Didn't find that one yet on google.
Forgot to add, it needs to report two times a day for audit records,customer requirement.
Are there stand alone monitor systems that we as business owner can purchase to "sell" to customers?
Need to "babysit" 12 walkins.
Your tuition for the dishwasher course is due.
Please send $150.00 to my address.
Hobart built the units with a heater hose drain.
Also the unit does use an air gap device on the rear.
Drain issues like E5 can also come from the discharge height of the drain connection, the...
Make sure that "goo" has not got into the boards/wiring in the pull out tray.
Have seen goo work itself back under the top surface and drip down
Also assuming the operators keypad is tight...
RUN Fishintime, RUN...............as fast as you can the other way.
Classic case of you being used.
Suck you in , get what he can, spit you back out, all for his gain.
Charging........IF the condensor is located in the unit ,then the nameplate data in oz's should be used.
Condensor remote?, then line size and length comes into play.
Appears to be made like a...
"older" places might not even have makup air.
Can't pull out what you don't have.
It's all a balancing act betwen the proper air flow out, the proper air flow in, while keeping the A/C affected...
Time is money.
Will take longer to mess around with a TXV swap and the unit really won't care.
Who made the unit, what gas, how clogged was the cond coil?
Get an OEM tube(s), clean...
Not being a butt here, but I don't see this as the customers problem.
Jumping ship to A/c just closes one door and opens another.
Walk into a "name your customer...
Take a camera and get a picture of the seperator.
unless you want to accept the responsibility of a patched electrical job.
If you find a brand of oven that does cook even, please let me know.
All the major players ovens will cook uneven stuffed full of sheet pans.
There is no way to stop it.
Air can not pass...
Built in's work fine IF the customer/users operate it correctly.
Worse thing is "cold"grease left in lines, pain to clean out.
My only gripe with Frymaster is they wrap the oil lines with heat...
Life is to short to mess around with hacked cap tube systems :D
The systems are designed on the ragged edge, cheap.
In your case I would have ordered OEM captubes, cold control,and bullet...
Do you have a history on the unit , if not:
Make sure cond fan motor is correct, look like a replacement?, correct rpm,s?
Verify with a amp draw of motor, make sure it's working, not just...
3M part number is 610
Comes in packs of 50
3/4 x 24"
Bally uses strips made by 3m
Call Bally and get the part number#
Just laid a new 18 x 23 box with them.
Just wondering how you will get them to stick on a cold wet floor??(and have them stay...
I service 3 school districts, this year every steamer will have a Kleen steam attached.
They just work, period, if maintained.
For serious de scaling the everpure bags are the way to go.
Well in this area hot guys make more than normal HVAC/light ind techs.
There is nobody local that does racks so I clueless there.
Have serviced Hot since '93 mixed in with cold,...
+ 1........yep, just what James said.
If you don't go through the process it will come back and get you.
My self, cap tube systems for the last 15 years.
Checked in on the freezer yesterday and found the box at -4 with the compressor cycling. :yes:
I lkie things to be right on so let me pose a question.
Still have ice formation at the condensor,...
Installed valve kit and fired her back up.
Sounded different, picked up discharge temp to 148.
Down to the box for a SH check(after running a while)
SH was 12 so a little adjusting went on...
Been many years since I put a valve kit on.
Are the torque specs included?
Did a pump down..............after about 30 sec the ol compressor finally pulled down to about 2" :eek2:
So needless to say a kit will be here tomorrow.
I guess a pump down just...
Compressor is semi hermetic 3ABA-031E-TAC-222
No product in freezer
I may have messed up this morning doing the super heat, was in a rush.
May have picked up the wrong number on the old chart....
measured psi at evap was 29
5 deg temp was suction line 10" away from pressure port on the vertical.
Used my new Fluke clamp probe on a reliable meter.
I don't think there was insulation etc...
First post , tho I read as a guest.
Like to run this problem past other techs, I must be missing something.
New customer, about 6 mths, no work on this unit till last week