Type: Posts; User: douknowq
No No No, the arrow is for "inlet" like an accumulator..you just solder the other end shut
I took the cover off heat pump once and there was a pigmy rattler stuck to the service fact envelope between the elec cover and outer cover i vas of course face to face to him about 10" away...he...
Have no idea if my emails r getting through have never heard anything?????????
how do i check my progress of pro membership, and even if they got it?
how do i check on my pro statice?
r there a lot of diyer asking about superheat, subcooling and suction line restrictions?
ok I understand
so should i ask the question in commercial? because this is not helping my customer now. I would understand if i was a home owner but I have been in this business since 1981. I am not asking a...
license # CN209477 Ga. State unrestricted commercial, industrial and residential.
I am just trying to fix a customers problem
Draw the line?????? MO is the one who got right. if you don't know the answer then say so.
I think Im going to have to rethink my commitment of the drake equation
Glenn Sepelak, Georgia American A/C. look it up
I am not a diy.... applied for pro member already. I have a class II unrestricted license
System is 3 yrs old, heat pump. When I got there it was running @ 225 head and 30 on suction. I disabled the blower to check the the txv on evap. all lines frosting on distributer so no blocked...
Some guy's just don't read the GIANT RED TAG!!! they put on the suction valve I guess. Why would it hurt the compressor with nitrogen in the system??? I know it does not work with it in there...
way 2 go Meoberry
The Winner is..............MEOBERRY Yeaaaaaaa
was nitrogen that was not evacuated from condenser when installed. I checked on this unit and it comes with nitrogen in it when new... no...
cannot figure out how 2 do it ...... have unrestricted class 11 license but the form says print out and email ...if i print it out how do i email my stste license and epa card?
now we r getting some where. I had planned to recover freon ..pull a deep vac and put all new gas in to eliminate possibility of non condensables.
by new i mean only installed last year.. i do not think it ever worked in the first place... sorry if i was short i am tired and looking for some answers. it was installed in the fall and i am new...
i think it is non condesables even though the sight glass is green. i thought maybe someone would have an opion instead of questiond of sarcasm.
make sure the refrigerant flow is left to right
pretend the sight glass is not there
seems like it still needs freezone ( with 350 head pressure)
how is this helpfull?
where did the refrigerant go???????? did not go anywhere ...system running when i got there...not running well but running