Type: Posts; User: digo
Search: Search took 0.05 seconds.
They've come a long ways, but still not perfect... software wise. It's a little bit of a love/hate relationship. If you're new to the product it's not so bad.
Gee, I wonder how come no one mentioned the Spyder yet... :rolleyes:
Here are a few other links:
BBMD article by Bill Swan (Alerton BACnet guru who has since passed away)
Contemporary controls pdf titled What is BBMD and Why Should I Care?
It appears the the web feature is unlicensed, which means you won't be able serve up graphics to a web browser.
Beyond that, the JACE is having a problem initializing the RAM disk, which is where...
Go to Platform Administration and click "Change Date/Time"
Click "Use Local", then Save.
Go to the File Transfer client and browse to niagara/lib on the JACE (right side), and browse...
User dana (Tridium's hardware engineer) explains what you're seeing on this thread:
I'm assuming this is coming from the fact no one responded to your question here:
EBI is a branch only product. There may be only a few Honeywell contractors who stuck around with SymmetrE...
03-05-2013, 04:43 PM
Damn, is that a one minute timeout?
Sent from my MB886 using Tapatalk 2
03-05-2013, 03:55 PM
Once your post count is up and you apply for Pro membership I think that becomes an option...
02-26-2013, 12:16 PM
bacnet id defaults to 1338... leetspeek?
02-23-2013, 02:56 PM
from that last link:
When using declutch, return to minimum mechanical stop. Part of their new adaptation function, read up on 63-2633
Also there's a service switch that should be set for at least 2 seconds prior, or...
My cross reference search shows the L7033A1207/U is the direct replacement, but didn't see it as available....
Our rule was to not start work on SymmetrE on Fridays. You could easily start on a Wednesday and still have a 30% chance of still being there on a Friday... no joke.
I too cut my teeth on CARE 5/7 and SymmetrE R300.2 and R310. Database synchronizations with CARE, on large campus networks - think dozens of ilon600s with multiple point servers - was just a...
SpyderTool 5.201 or later eliminates this nonsense. Basically the tool is initializing the control logic on station startup (think opening up the controlLogic wire sheet) on each spyder.
Sounds like you just need to reinstall all of the existing modules for the filter to apply. You can do that from the software manager view. Highlight all of the "Up to Date" modules and click...
02-11-2013, 11:04 AM
java.net.ConnectException: Connection refused: connect
The connection refused tells me it's likely an issue with the fox port not being open, or the incorrect port # being used.
If it were a...
02-01-2013, 05:44 PM
Can you not access the link I posted abbove on niagara-central?
read up on docs\EngNotes\LinuxSupervisor\docEn_LinuxSupervisor.pdf
To start the platform daemon:
really? 1 year warranty is standard in our channel, I'd expect that to be the case across the board, considering hardware-wise it's the same product across all channels.
The installer shell script is meant for RHLE 5, which distro are you attempting to install it on?
Not counting the ECC patch issue from a few years back (field recoverable), I have run into this only once in the last...
Correct, it's simply saying to keep the power for the ndio isolated, when using the IO-34 module. So in the case of your CO2 sensor, don't use the same power supply that powers the ndio.
Results 1 to 25 of 500