Type: Posts; User: newgage
Search: Search took 0.01 seconds.
Does anyone have access to a Lennox wire diagram?
Model: GCC16 060 120 4J
S/N 5602 G 08158
Sorry,,, I was actually looking for the slimzone Premier Manual.
Does anyone have a link to the manual for this system?
Anyone have any info or links for a dehimidifyiing air handler going under the name Chinook.
Model: Phi Beta DH25
There are two Actuating valves on seperate condenser water outlets....
Pulled the heads off compressor #2 today. It was nasty nasty. Top of pistons were pitted really bad. Copper plating around discharge valve seat. One head had a missing spring plate behind the discus...
The oil was good - no metal flakes. It was darker than the other circuit yet that was what I was trying to clean up. It has a history of dark oil on this circuit which is getting better yet still...
I was changing out the drier cores in a Mcquay Alp 150 and found chunks of valve plate inside the drier shell.
There are two circuits 75 tons aside.
Each circuit has two 35 ton coplemetics (6D...
Check my contact info then send me an EMAIL. Then I will send you the PDF file. Try Again.
By the way unit is operable now. It was the sensor!!
Send me an email and I will forward it to you.
I have an issue with this unit occasionally tripping on low water temp fault. I now know the leaving water temp sensor is a 10,000 ohm thermister and I can check its resistance at a given temp to...
This will help a lot and is greatly appreciated. Not even my trane supplier could provide this to me.
You Da Man!
Thanks Willf650 . The model is GEHB03032H0120RLC.
Can any one give me a link to read up on these controllers. There is a test and service button on the board. I would like to know what the procedure for use is.
I changed the water filter and have the flow to the top resevoir pretty good. The flow from the distribution tubes to the evaporator cylinder is just right.
The problem is the lower water recovery...
Its definately not off of the top bowl. This might be part of the problem.
I have adjusted the ball valve wide open and can't keep the bowl more than 1/4 full. Without enough steady water flow to...
Howe Ice Flaker By Scotsman
Model: 2000 - Rl
S/N 13597 (1993)
I got a call to work on a Ice Flaker that had damaged distribution tubes. It turns out the "unit iced up". The guys on site -...
Correct on the GE part - it was in my notes but miss posted that part.
Airflow, I agree sounds like an issue. TD is quite high.
I am certain the water is treated and has qycol. I will find out...
Trane, Model: HB03032H0120RLC , Sn: W03c09297
Board: Tracer : Zn 5.10
I have a pump that is going off on Low leaving Water Fault. The loop is on a geothermal setup. The building manager tells...
I am looking at picking up a used hammer drill. Boss said he won't buy me one. It is mostly for 3/8 concrete anchors. I think a hilti te5 is what I want.
What do you guys use?
The cost of a new one is very reasonable.
It looks like a good back up for my H 10.
If its quality and performance is good I may get one.
I saw this on ebay.
Anyone have one? Comments?
Thanks Baldloonie. I didn't know that.
I gave air mechanical an answer off the cuff. I guess I should have done some research for his pop quiz. I am quite sure my supplier would have informed me...
Honeywell Vision Pro 8000 series - my favorite because if its versatility.
No, I have four years experience in the trade. Just wrote my red seal exam and passed with flying colors. I mostly do commercial Hvac and refrigeration and have very limited residential experience...
Friends older house getting renovated with insulation and windows.
Heat loss/gain calculation : 48,000 BTUH Heat loss, 18,500 BTUH Heat gain
He wants duel fuel.
He wants variable speed.
Results 1 to 25 of 135