Type: Posts; User: babyboy23
ok the compressor did go bad. so it could have been that.
I was working on a Freezer. I found Compressor bad. replaced Compressor and filter line dryer. found liquid line dryer guts busted up. it stoped up the line befor the txv. what would cause the...
hvac buddy sound good. Does it help you trobleshoot some probles
just looking for a good app to have.
I think a lot of problems is peolpe dont have pm done. dirt filter was the most thing i found the most.
i whould run from that job.
i need install manual for a carrier t-stat. looking for one to download.
the m#-33cs2pp2s-01 thanks.
i whould run from a place like that. there whould be money to make. but i dont think that place hould spend the money to fix all there units.
i have never seen a unit that bad. that is just amazing.
I was working on a heat pump today. I replaced a defrost board. This board i put on had a 5 min delay. It was on a Evcon. Is it just on that brand. That is the frist one that i came a cross that...
I whould get r-410a. it will be hard to find r-22 and the coast will go up on r-22.
i am suprised that it did not kill the compersors in them systems.
nice video that is the worst duct job i have seen. i dont see how anyone could walk away and say i did a good job. looking forward to the flip.
i work on them. the company i work for has a lot of them. dont have many problem with them.
i have seen some dirty filters but that one bad.
when a scroll pull down into a vacume how does it break the compersor. i had one go bad because the presure switch went bad. i know it bad for them to go in a vacume.
it not the compersor. the coil u have only works for 410a. it does not work with r-22.
you can mismatch system but when you have an 10 seer coil on 13 seer out door unit. you will be replaceing compersor on it.
Has any one come a cross where 13 seer out door unit was installed on a old 12 seer or less. where i live i have hard of a guy doing this to peop:(le.
he going to try to save $. but in the end he will spend more $.
i have only seen one of them. it was the bottom of the line unit.
call pro to come out and look at it.
i have cleaned ge that old. them thing laast forever.
i have seen that done on equment. i dont know why anyone whould do that.