Type: Posts; User: mark 11
Search took 0.01 seconds.
I think TRUE has the best gasket design , just pull
old gasket out of channel, and press new gasket into
channel, no screws no hassle, why cant they all be designed this way, definitely easy...
I went back in 1998, made it a vacation combo with my
wife,checked out Atlanta, Stone mountain, any way the
Hoshizaki advanced seminar was pretty interesting, at
the end you get a tour of the the...
If they last well past the warranty replacement time
thats good enough for me, we dont want them to last for ever do we??????
When i get a customer quoting me my cost on parts or
equipment, i tell them ok ill install it at that price,
ill be back in evening with part,when they call in evening
to ask me when im coming...
Thanks for info NDFROZEN, it is amazing to see what
a difference new insulation makes, i once had a customer
with a 7 by 7 walk in freezer that would not go below 28
degrees, my dad sold them new...
I lost a replacement refrigeration system Job for a
Mcdonalds walk in freezer to another company,
this company installed new complete evaporator and
condensing unit system, i was there about a...
I once had white ice on a Manitowoc machine, problem was
burned out dump valve coil, white soft ice was from extreme
concentration of mineral build up in water............
Just include the time it takes you to go to the supply
house in your hourly rate, customers pay big bills
more willingly when they see it took you a long time to
fix there equipment, you can only...
Just wondering how many of you fellow techs have had
walk in freezer service calls in summer where every
thing checked out normal, super heat, subcooling, pressures
with in normal range, defrost...
Thank you very much for that information SNEW MAN 24,
im going to talk to that york counter guy in person
Monday and show him the print out of the 13 seer
one ton units he told me they dont carry...
Any body know where to get 12000 btu a\c condensing units,
bought the last one from Johnstone,[ discontinued ] i was
told York carried them but when i called them i was told
they dont, did i get a...
I wonder what a HeatCraft 4 blade blower evaporator
would look like mounted to the bedroom ceiling,
maybe just cover it with some fancy wall paper,
a could get very creative with a customer like...
The future belongs to the Scroll compressor,
lighter, stronger, better,more efficient!!!!
Ive got a liquor store owner customer with a Hoshizaki
ice machine with evaporator separation like that, its
bin filling the bin in that condition for years,
it is amazing how they will...
One huge advantage of having 2 completely separate
systems is the the odds of both of them breaking down
on a 95 degree weekend would be extremely remote,the
house temperature would be tolerable...
I had a customer that had me replace his 4 ton scroll
compressor with a piston pump just cause he did not
like the sound of scrolls, he paid full compressor
install price and i found a new home...
Thank you guys for info,end of long day, read it upside
Any of you fellow techs know what tonnage a 890 goodman
piston is rated at????? thank you!!!
Do any of you fellow techs know if a typical water
softener system will have any effect on your typical
commercial ice machine water filter, had customer
with home Manitowoc QM 30 ice machine with...
I worked on that same machine for a customer around two
months ago, same problem, it was a ICE O MATIC, same
machine with there name slapped on it, Ice O Matic
will ask double the cost for parts...
Any of you fellow techs using a ultra sonic leak detector
on a regular basis, had this sales man ive known for years
let me try out this DRACO DL10 ultra sonic leak detector
for a couple of weeks...
Update.......went to check on machine today, cycled off
on full bin, normal operation, it was old float assembly
sticking closed, im going to start installing new float
assemblies instead of...
IT is air cooled self contained, 40 psi flow pressure,
going to install new harvest float assembly to eliminate
possible intermittent sticking,any other ideas??? also
unit located in back yard of...
Hoshizaki KM 450 r22 unit, unit shuts down every day on
3 beeps,[ freeze back up timer ] installed new water
solenoid valve, cleaned float assembly, clean evaporator
coil and water...
$1000.00 dollars for crane rental? is that a Mercedes
I just thought of solution to by question, 110 volt
solenoid valve in drain line wired in series with
condensate over flow float switch, i know this may
sound radical but i'm not drilling through...
Any body know of any make of condensate pump that is
completely sealed, the problem with using standard
condensate pump for ice machines is if you loose
power to unit, melting ice water will...
Just the load of the contactor coil less than 1\2 amp.
Didnt loose the charge, just blew the the top off
where contacts are, this is those little cylindrical
type with apoxy sealed where wires enter, it was leaking
refrigerant but real slow, pumped it...
Was checking out Scottsman ice machine today at a
McDonalds for no production, found open low
pressure control, bypassed control with jumper,
contactor pulled in, about 10 seconds later low...
Im a Dan foss fan,i love being able to vary capacity
with simple change of piston,stainless steel body,
thin capillary easy to route.
Charge customer full price, tell them when you receive
check from manufacture you will refund the amount,
if they dont agree,tell them to call you back when
they change there mind, unless this is...
why not just mount regular bin stat low in storage
bin against side wall????
When i get this request i just tell them im booked,
and give them a competitors phone number that i
Hey gomer your last name wouldnt happen to be Patel?????
I wish aluminum coils didnt exist in this trade,
if you can get to the leak with a copper coil
you can fix it fast, why cant they all be copper???
I cycle the condenser fan on and off in cold weather
to get my head pressure in normal range,any body else
use this method???
Ive repaired dozens of restricted cap tubes by cutting
off a couple of inches of cap tube at entrance,with
new dryer,good luck!!!!!!
[Edited by mark 11 on 03-11-2006 at 11:19 AM]
Thanks for replies guys,really appreciate the information!!
Any body out there have a lot of experience changing
home refrigerator gaskets, ive taken on this job about
a dozen times and never got the door to close and seal
any where near the factory...
Dont sweat the small stuff, and remember its all
small stuff,,just think of all the people out there
out of work and the rents way pass due,i look at life
as one big exciting game,and the more...
Well i have to agree with you 100% Ro bo teq on your
thoughts about change, those who cannot deal with change
are doomed to failure, you've got the Rocky theme song
playing in my head, thank you,...
The phase out of 10 seer units just plain sucks,
its like the phase out of R 12 with no alternate
drop ins, i wish the government would focus on
more critical issues like skyrocketing health
Thank you all for replies,like i said im all for doing
the install perfectly matched the first time around,
i hate call backs with a passion too,i guess im just
going to have to accept that the...
Were talking about customers living pay check to pay
check,bad credit, yes i know i will have zero problems
installing matching 13 seer air handler,if every customer
i had was loaded with great...
Ok this is the situation, say you have a customer with
old 10 seer heat pump condensing unit with major compressor
burn out but has recently installed new 10 seer air
handler with piston feed, 13...
How big is this house? $25 dollar electric bill to cool
your house, is this house located at the North pole?