Type: Posts; User: Garyhvacr
Search: Search took 0.01 seconds.
Need more info.
Thanks chad nc
Thats 1 I didnt think of. The other I learnsd may be a bad TXV over feeding the evap causing liquid freon to be coming back to the compressor and washing it out?Herd of that 1???
There is a product used for small leeks. Its about the size of a pen and works like a septic stick. I think you can use a heet gun and rub it on.Never used it ,Dont know the name but have seen it on...
Inhereted a headache100 Ton air cooled York chiller(2 JZ compressors)
Circuit 1 compressor going off on low oil pressure every 5-6 hours. Oil is below site glass when I restart and returns after...
Results 1 to 4 of 4