Type: Posts; User: walters
Search: Search took 0.01 seconds.
01-22-2006, 08:47 AM
Thanks to all of you friends and a special thanks to Icemeister!
This is my first free Sunday since 2 month…
The Ice-cream cooler is working perfect since almost 4 weeks. I’ve rewired the defrost...
01-19-2006, 07:39 AM
Sorry for the late update, I am still quit busy...
Thanks everyone – a special thanks to Icemeister!
I’ve installed a timer, set to 4 cycles @ 30 min. It works just fine, but I need to clean the...
12-30-2005, 07:09 AM
Great job Icemeister, thank you very much, you've spent a lot of time with this clear and easy to follow instruction!
I know already that some technicians miswired (to be mild...) this unit. The...
12-29-2005, 08:00 AM
I'll check the honeycomb again today, at the beginning (before freezing) the air-flow apeared to be normal.
I definitely install a timer without heather and controls - thanks t527ed and thanks to...
12-29-2005, 07:51 AM
The mod.# is RCA 2RU - ser.# 9796-0114
The unit has been serviced several times from different technicians but never run without problems, according my customer. The unit freezes and won't go in a...
12-28-2005, 01:04 PM
This is a fresh meat display cooler, very old and probably converted a couple of times. The evap freezes on the u-bends.
I will take SH measurments tomorrow and also check the TXV's.
12-28-2005, 07:29 AM
I don't know much about this unit; the owner changed a few moths ago. The new owner contacted me instead of the previous service company, they’re 60 miles away.
The sight glass is clear, the unit...
12-27-2005, 08:11 PM
This is an old unit, converted to R22 refrigerant a while back. It has a pump down valve, but no defrost system, at least it’s not working; the wiring has been modified from a local bricklayer…
12-21-2005, 07:59 AM
Sorry for the late response, but I am sooo busy this time. I have a new customer; a small local food market with a large ice-cream display freezer. A technician installed a new Trenton condensing...
12-19-2005, 08:17 AM
I am working on a Hussman 5-door display cooler (Ice cream). The unit freezes up. The charge seems to be OK, 200 / 20 Psi – R-404A.
The defrost system has a paragon timer; electric heater strips and...
Yes, they're brandnew and match the capacity. I'd like to convert one of them to R134a. You think this will work?
I would have to change the oil to PE, no problem.
I always thought...
I have several R22 rotary compressors on stock, .5 to 1 Hp, outfitted with AB or MO oil.
Could I use them in medium or hi-temp refrigeration applications, using R22 or a different refrigerant?
Thanks jhd1234 and selfemployed,
You both are on the right track.
I would like to install a drain system with a pump, the condensing unit is on top of the walk-in; actually in the attic with...
I am working on a walk in 6’x10’x7.5’ Polar-Pak by Kolpak. It’s a beer and food cooler for a hot wing place. The stat is set to 32 to 40º, there is some frost build up on the evaporator from opening...
Bryan - thanks for the reply. But I can't find AeroBell electronics... Please try to find a bit more info on this; I am sure many others would like to a find a cheaper replacement battery!
After many bad experiences - I use my H10 and nothing else - period!
Please let me know where to get the replacement battery - thanks - walter.
Results 1 to 16 of 30