Type: Posts; User: RACLman
They are Honeywell W7751B XL10 VAV controllers.
Controltec, if it's not too much trouble I would like to get a copy of the manuals as well.
If you had the XL10 configuration screen available in AX then the Wizards are already installed on the JACE. The Commit button only saves the changes to the AX database, you will still have to...
If you already have a complete database in AX why would you want to bring Lonspec into the picture. Why not just load the Ax Wizards on the JACE and modify the XL10's
in your AX database. Seems...
I would like a copy as well if it's not too much trouble.
As of 2009 when the App was last updated it was not compatible with Rapid Balance. It does have instructions on how to perform the balance proceedure included in the App's documentation.
I believe it is found in the snvt nvoStatus and is called manualControl. False = Auto, True = Manual
Just received my e6520 2-weeks ago. The legacy port replicator attaches
to the docking station connector on the bottom of the laptop. has worked
perfectly so far.
Thanks for the responses. Unfortunately I am unable to upgrade the 3.08 LNS database as another contractor is also working on the system as part of a phased upgrade of the controls. The other...
Is it possible to run LNS Turbo on a Windows 7 PC with another version of LNS (3.08) running on a virtual Windows XP OS on the same PC?
Will the two coexist or will they hose each other up?
I believe the BACnet Spyders auto adjust thier baud rate to the JACE when they power up. Cycle the power to the Spyders with the JACE up and online and they should syncronize themselves with the...
Ditto on Quicksilvers Driver. Works well.
I also was certified in 06, back then the highest score was a 149. Go figure.
Hope everyone has a safe and happy holiday
LonSpec v5.1.5 does support MS Windows Vista and is available for download on the Honeywell Buildings Forum website.
The VAV1 or "1000 Series" XL10 VAV controller is not compatible with RapidBalance. The VAV1 pre-dates the use of E-Vision. This controller was programmed and commissioned directly thru the Zone...
Honeywell has a Lonworks based package called RapidZone for VVT. It's simple to setup but requires an external dry contact closure for scheduling as the AHU/RTU controller (XL15C) has no real time...
That sounds dangerous, sharing anything with EBI is problematic at best. How many lon channels are you dealing with and where does the 600 reside in all this?
What version of iLON? 600, 1000, Etc...
Verify what version of the PCC-10 driver you are using. I have found with running E-Vision in WinXP that you must use this version (pcx10_20Win2k_Ver2.01_B) of the driver and not the latest and...
I'll let you know, I'm going to be trying it in the next 2-3 weeks.
Just upgraded 5 WEBS JACE-6's about 2 months ago from 3.2.16 to 3.4.43 and they only charged me the single upgrade price on each one.
If you are running MS Intellipoint software on your machine you may want to
uninstall it. This has corrected the problem for some who have experienced it.
Takes about 15 Minutes and that includes the on-line licensing.
If you must keep the controller you can buy a copy of XL-Online which will allow a PC to connect to the controller directly, (no graphics but will get the job done). If it's only 1 controller the...