Type: Posts; User: rowens
Would you like a 10 1/2, or 12?
With an old cap tube evap, a subcool of 20 is normal.
Have your tech test manofold pressure to see if it is set correctly.
Shouldn't that be a 4x4?
After 35 yr. doing HVAC, what do installers say when issues like this come up? "Looks good from my house."
And another dog has expressed his opinion of A/C, that he doesn't get to share.
yes, i think that one is shot
That must have been interesting. I would think that using a 1.5 pole on a 3 phase compressor would cause a single phase.
Why would anyone put a 3 pole contactor in a single phase unit, and then only use one pole?:rolleyes:
Problem could be caused by a bad compressor, or a loose connection.
Looks better than an Armstrong oil pac that I condemed yesterday.:(
If you are increasing the size of your A/C unit you will have :
1. Replace existing ductwork, or 2. Add to the existing ductwork.
This is necessary to move enough CFMs for your larger A/C unit to...