Type: Posts; User: stkepo
Search took 0.00 seconds.
well it sounds to me like you may be working on a chp20 lennox php? if so there are 2 pressure switches in the low voltage.1 is for defrost termination and the other is standard pressure switch.there...
by looking at the model # on a/h is that a 3.5 ton?
if so the txv your using may not match outdoor unit.
56j19...1 to 3 ton
56j20....3.5 to 5 ton
could be issue with superheat
also check cfm!
lennox is charged by approach, is indoor temp high? check charge by approach method if indoor temp is high i have noticed high superheat...lennox sometimes gives you an subcooling chart on there...
if it is a downflow airhandler the coil on the cb29 and cb 30 models have to be flipped upside down....
when this is done lennox provides to metal drip shields that have to be installed on the...
well mr dalton all facts you stated are very true if that deep of detail was needed..
not sure what was meant by the post, but fact still remains
99% of the time there is a reason for the...
look guys we all know that it's highly unusual for a pressure switch to trip for no reason.....but we also know that it's a mechanical device and can go bad...
in my 15 years in hvac i may have...
yes temp prob good and secure
i can't figure it out super heat will hold at about 16 degrees for about a minute and then will drop to 2 degrees on a fixed orfice. blower speed steady and suction...
what would cause an unstable super heat on a fixed orfice coil...blower running fine .evap coil clean
suction pressure steady at 80 psi but superheat changing from 5 to 15 degrees .head pressure...
thanks for the link it's a big help......
thank all for the knowledge
14 years and i'm still learning
guess i always will
i've read the little book that comes with them but all it tells me is about hp not rpms
we use the first call motors from lennox
thanks i will try to fine more info from lennox
ok i think i have it...
so changing the speed taps on a multi hp motor only changes hp and not rpm....
i understand all about the rpm and hp was just unsure about if the rpms were changed by the...
head was around 285 suction was 80
ambient was 94 cleaned coil head went down to 240 and suction dropped to 75 and has been cooling fine with no pressure trip.....also was a 5 ton lennox gcs rooftop
i ran into the same problem about a week ago and i did replace the motor ....and i was back 2 days later...
even though the condensing coil appeared clean it was not..
i cleaned coil and has...
on a universal motor (condenser motor)
it can be used for 1/6 up to 1/3 hp by changing speeds..
and caps the motors are rated at 1075 rpm with 2 speeds
if lower speed is used for 1/6 hp does it...