Type: Posts; User: crow1
Has the navigator been sold yet?
Update: I just returned from the sight a few hours ago. I checked all the wiring to include the motor. Everything megged over 500M ohms. No issues there. I then called Danfoss tech support and...
jayguy, I want to thank you for the information in regards to the Code 14. This site is the BEST. I will also try to get ahold of Danfoss technical support to see if they have any other info...
I have to leave before the crack of dawn tomorrow morning. Does anyone have access to this Trane Alert?. It would really help me.
You can find a great deal of info on all compressor makes under a web search for (brainerd compressor).
Yes, it's Trane Intellipak, Mod# SXHFC304. I'm told the unit is approx 7 years old and they had to change out the original VFD about 3 years ago. Do not know what was wrong with the original VFD.
I have been tasked to go out of town (150 miles each way) to troubleshoot and on-going issue with a TR1 VFD. The problem the customer is having is intermittent Alarm 14 Earth Fault. They state it...
I have been trying to locate a copy of the programming troubleshooting guide (SAHF-PTG-4A, dated Jun 1999). Any help would be appreciated. Thanks.
OUTSTANDING. Thank you!
I am in need of of a York service manual: 160-54-M1. It's for a centrifugal chiller. I have posted my e-mail. Thanks for any support on this. CROW.
Would this unit happen to be in Casa Grande?
e-mail is . Thanks. CROW1.
Dapper, I actually would like an American version. Thanks. CROW1
CROW1, Marty, Tucson, AZ.
Thanks for the update cagedodgeman. I did charge the unit and cleared the sightglass. But when I went to measure the subcool (both at the exit of the condensor and the receiver) I did NOT show any...
What's the proper procedure in charging a low-temp walk-in box with a TXV,sightglass, and RECEIVER? Do you measure your subcooling BEFORE or AFTER the receiver?