Type: Posts; User: brucew
I'm learning service.
I was wrong. It's a flow check piston.
thanks for responding. Unit has a capilary tube.
I have a Rheem 2 ton split heat pump that is shutting down on high head. Bypassing the HPC allows the comp to run and pressures are 225 high and 0 low. After a few minutes the high pressure starts...
I'm troubleshooting a RHEEM packaged heat pump, 13 years old. There is no control voltage coming into the t-stat. The outdoor unit breaker has power. Is the control transformer the likely culprit?