Type: Posts; User: oshieldsa14
replace it valves are bad compressor gone
Your right but the problem wasn't the flood was it? It was after the flood when they drained the system and refilled it. Or did they even put any water back in the system. Maybe not a air problem...
yea its called steam locking or air binding
I think you may have air in system.
Has anyone ever tried to right a program to run a intellapak instead of just giving uint a start/stop?
Haven't seen field assistant yet either. Only real change sales man showed me is new gfx.
Is loop temp high? I would start there then go to water flow. Water setter could be set to low or could have stopped up lines. I've had to back wash a few with the same problem.
I am thinking of up grading my WebCRL to the new 5 from 4.1 just wanted to see if anybody had made the change and see what they thought.
ALC is not proprietary.
The help file helped me alot when I first started with ALC. I printed the file and gave to other techs where we could study it.
Email Address Removed or call 770-795-5177 Maybe this info will help. The training is a little high but it is worth it. Your installer may not like you bypassing them but these are the guys who...