Type: Posts; User: Tommy1010
mistake....new module is 780-845
friend of mine had to replace his ignition module on Lennox unit model # G20Q3E-75-4
the original module was SP745 robert shaw
the replacement part they gave him is also Robert shaw 80-845
how many wires and what colors are they?
your not being very accurate with your name calling, it's O-blame-o
liberals will never understand, spending cuts leave extra revenue to work with
no need to raise taxxes if you trim the fat (waste)
also if regulations are loosened this allows for more jobs...
Lennox 3 ton rooftop package... LP gas heat
honeywell VR8245M2530 smartvalve
Tries igniting but valve wont open. Gas was verified to be present at inlet of valve.
All safetys are closed and 24v is...
when you get a flat tire, do you;
1. change the tire
2. keep driving for four more years and see if it gets better
Ok folks its time to refelect, its time to take the facts, and accept them.
You know in your heart what you want to pay for gas, you know in your heart how much your dollar is worth, you know by now...
hmmm, sounds a little sketchy
i was taught to remove all control wires, use little popper as a resetable in line fuse
put amprobe on the 24volt wire at transformer, start attaching one control wire at a time as you energize its...
cracks could develope anywhere, an inspection cam is a wise idea
the possiblity that a little tweekage in the tstats installer set-up mode may help
yes i have 445 on 460 unit
Supply Voltage concerns me a LIL...445v
fan pulley also caught my attention...seems small...but its the standard from carrier..
Carrier water cooled omnizone package unit
brand new install
blower motor rated at 4.3FLA...pulling 9.1, tripping safety reset on contactor
remove belt motor pulls...
I have a certification question
My plant (steel mill) wants me to work on there mobile equipment Hvac systems. Big tractors and graplers etc... I dont want to , its greasy up there HOT as hell and...
thanks fellas, good info
Been installing alot of new WATER COOLED units here in my plant. In the past we've had alot
of issues with high head pressures and cracked condensers due to scale build
up. Most of our lines...
relax, the people have spoken, apparently you did not like the decision
tough shanoogies, get over it, and play ball or sit on the bench queitly
can anyone answer this?
isn't suspended with pay just another paid vacation
answer fix the economy first, then the debt, then the deficit, then worry about healthcare
they are only ruling on the mandate part of Obamacare
i would tend to think CFM and amperage would be the same with both motors
but won't the higher horsepower motor need more cfm to stay "as cool" as the lower hp motor
if i needed more CFM...