Type: Posts; User: mikeduncan
i had a problem with water furnace sending the wrong size txv it made the compressor slug mostly when the dhw light was on.
jw3 and fp1 are the same when cut it drops the temp
Join Date: Oct 2009
the carrier booklet chart says it should work with water temp down to 30 bet water in temp at 40 it shut off on cold water/low flow...
i have installed and worked on climate master and (carrier) which is made by climate master for ten years there have been some problems fp sensors ging bad are the most common problem. the problems...
in theory it would work but the problem is you can over heat the compressor and lock out on high head. if you were to use another heat exchanger for the ground loops only then you can increase the...