Type: Posts; User: pimpdzl
Thank you guys I got was the txv filters that needed to be cleaned and adjusted
Semi hermetic with two evaporators at 30 suction 300 highside so taking freon at those readings evaporators are blowing at 48 degrees
I'll try to get you those numbers today and i'm confused about the reference and what sh is
Sight glass is clear no bubbles im not near the unit work two jobs for all the numbers just know that same evaporator keeps freezing up its a 404 unit
Hello I have a walk in cooler with one semi hermetic compressor and two evap units pressures are reading 27 suction 300 high outsider temp ranges from 90 to 100 with about 60 percent humidity one of...