Type: Posts; User: dracula
Search: Search took 0.01 seconds.
I am slightly biased towards products you can get without being a "licensed dealer or distributor",
and those that are easy to have my end user clients learn. With that in mind here is...
04-27-2013, 12:43 PM
Are you familiar with soap and xml pipe feeds?
Seems like you could aim a custom excel based soap / xml data pipe feed at the clients web based schedule xml objects,
(if they can be, or are...
i-Vu 6.0 is likely to be out in August this year and it will support most browsers regardless of OS;
Safari, Fire Fox, Chrome, at least that is what I have been told.
04-10-2013, 11:17 PM
Maybe a simple wall switch and the owner's secretary? When she get's hot, guarentee, she will hit the switch.
Sorry, that will not be a reliable control setup.
Actually, there are many dual...
Excellent! Looks like the tables were scanned in also.
Here is what the i-Vu CCN 4.2 Application Builder integration program would look like:
I can email you the actual program if you...
Just what I thought. I can almost guess that the Link you have on the site is a i-Vu CCN Link.
All you would have to do on your network tree is right pick on the "Gateway" and select
04-08-2013, 11:41 AM
Here are the Carrier translator files
04-08-2013, 11:36 AM
Email me and I can email you back the manuals and that show how to get into the
"config table" inside of the translator.
I would post the manual here, but I can not figure out how to...
04-08-2013, 11:17 AM
Can you post a picture of the "BACnet Integrator", as there are several different Carrier products that
ship in a Carrier RTU that allow for BACnet integration, and none of these Carrier devices are...
Ok, lets see if I understand;
You have what appears to be mostly CCN controllers, and someone put a "i-Vu Open Plus 5.1" frontend in to gain access to the CCN controllers?
If you have a "i-Vu CCN...
Application builder will allow you to "re-edit" a downloaded "Application Builder" program,
if it was created with App Builder, but there are some limiting factors. Many of the
Just a heads up;
If your installation is using "spong bobs" (slang for the BT485's) instead of the 120 ohm resistors
at the beginning and end of each comm segment, then you need to look into if...
04-05-2013, 11:47 AM
As with many BAS system brands, the ALC "Graphic Programming Language" is a combination of a
graphical display of the program, with the actual control program being in a format that is
Steve's comments are right on target.
One of the things I often do with a "repeated BMS comm segment" is to put in custom
"data handshake programs" into controllers on both sides of the repeator....
04-03-2013, 10:54 AM
I work with a very diverse group of clients, and the "owner/operators" of these BACnet systems all want the same
concept; no lock-in to one specific vendor product line.
This is what I hear;
Should work with multiple browsers
Live Logic with the Field Assistant Tool
BACnet Point counting GONE !!!! (I hope that is true)
One of the versions will be installable...
Learn how to adjust your "interface metric" associated with your hardware NIC and wireless NIC.
This will allow your browser to automatically adjust which TCP/IP connection it will use to connect...
Has anyone had a chance to test drive the Carrier i-Vu Open 6.0 version
comming out of Beta yet?
From what I have seen looks to be a substiantial improvement.
What I did not hear about is if...
Most of the "EIA485 to TCP/IP converters" that I have worked with, have to be configured to wrap the UDP Packets into IP packets (similar to the BACnet BBMD Function).
Not shure if this is...
ALC WC 5.2 has their own Field Assistant feature, very much like i-Vu, but as usual, more bells and whistles. The two systems are factory HARD Coded internally to keep the Carrier controls i-Vu...
1. Did you get their "ruinet" software to configure the Watt Stopper communications and points?
2. Read up on their sequence of operations; there are some functions that can disregard your remote...
Sounds like you are integrating into a i-VU CCN system. If you are, and you need to pull in points from the
CCN side of the "i-Vu CCN Link Router", you may need to add some custom integration...
Wow, your two questions worry me just a bit.
First, if you have not already started a dialog with your client's IT department regarding what you plan to
add to their TCP/IP network, I recommend...
Which version module driver did your RTU's have in them? ( you can do a modstat and post the screen capture here)
The program for the RTU's can not be opened or edited with i-Vu SNAP, as it is...
Are you using BACnet MSTP to integrate into the RTU's CCN devices?
I was not aware that Jace's could directly tie into the Carrier RTU CCN buss, which is a EIA485 buss, but the data packets are...
Results 1 to 25 of 210