Type: Posts; User: jonc
Edited. Didn't read the post throughly enough
Did you weigh the charge in?
Gerber diesel. My favorite by far
I wouldn't be as worried about the L wire missing as the Y2 wire missing. If that unit is a 2 stage unit.
I assumed he was using a equivalent f2rp air handler. I didn't see it in there either. Anyhow I wouldn't throw the equipment under the buss. Its prob lack of airflow like was mentioned earlier.
I looked in the install instructions of both units mentioned.. and i didn't see where they call for a suction line trap anywhere. I agree most manufacturers do call for the trap to be right before...
Hot-tap was a desuperheater made a few years ago.
I picked one up 2 months ago... helped me big time on an older carrier VS motor. Zebra determined the power pack was bad. Got the new pack.. hooked it up. Didin't work. :oops: I was in disbelief. ...
Sounds like you have a Straight A/C unit with just resistance heat. This guy has no competition? All the alarms are going off already. If he doesn't know what a manual J is who knows what else he...
4 years? wow that unit was prob still under warranty.
just wondering what happened to the 4 year old unit to warrant replacing it?
Looks great man!
Farmers should not be trying to fix your mothers heat pump.
That put a big smile on my face... rofl even my son said what the heck?
how would you fill those?
There ya go.
Went to this house yesterday and snapped some pics of a Aqua Therm unit that froze in the attic and poped the cover off the pump. Not sure how long it ran like this as the house is on the market. ...
May have released some oil when they disconnected there hose's. I'd say wipe it off and see if it comes back. Without low loss hose's and 410a on the liquid line it could get pretty nasty.... Call...
Why would this guy screw him? The coil is under warranty... how would it be in the warranty company's interest to replace it with a diff brand? Find out what the guys gona do before you throw him...
i remember these days... the service company i worked at had an answering machine for after hours calls. I prob don't have to tell you how bad it sucked. but you could call in and tell how far the...
rofl are you kidding? That's what the filter drier is for! :eek:
AND YOU GOT 30 MINS GOOOOO!
Saw this and thought i would share what i was thinking the service manager said to his tech.
Nice thanks for clearing that up... i was wondering how they got the temp low enough for the PVC vent but not condensate in the exhaust.
Guess I need to read up on my water heaters :p
that's nice. I would think it will eat threw the vent pipe in no time. Of course i'm not sure.. I've yet to see a 90% water heater with a condensate drain on it. But i'm not a plumber so i have not...
LOL.... Its been a few years since i've graced a maze home.
last one had box's to the ceiling and cloths hanging in the shower.:eek: And the maze had to be made wider to get the old boiler...
I've put in plenty of SSZ's this past year. No problems to speak of. To be honest i've been really happy with em... after chasing my tail over the york affinity evap coil fiasco :mad:
You get excited to hear the unit is in the basement.