Type: Posts; User: docent
extracting the maximum efficiency :)
Area - 10,000 m2
Rooftops with gas heating YORK - 20 pcs.
Productivity in the cold Qx = 1250 kW
Condensing units YORK - 2 pcs.
Productivity in the cold Qx = 53 kW
The customer had to be that way ... sometimes useless to explain;)
No, this is an exclusive and unique work.
Near the BLack Sea.
It's pretty expensive for a few months :)
Power - 704 kW
Area - 9400 m2
The absorption chiller YORK - 2 pcs.
Productivity in the cold Qx = 704 kW
Performance of heat Qt = 572 kW
Supply and exhaust ventilation units...
Power - 180 kW
Area - 700 m2
Rooftops with gas heating YORK
Power - 596 kW
Area - 12,000 m2
Air-cooled chiller YORK - 1 pc.
Productivity in the cold Qx = 462 kW
Ventilation installation Novenco (Denmark) - 14 pcs.
Air flow Ln = 59 076 m3...
Power - 1125 kW
Air-cooled chiller firm YORK with inverter control of screw compressors
Supply and exhaust ventilation units with rotary heat recovery
Power - 1946 kW
The area - 24000 m2
Air-cooled chiller with screw compressors, rooftop, Duct fan coil firm YORK
On test the site is made melting and amalgam fixing on an internal surface of a flask on special gold spots. At gold good adhesion (coupling of diverse liquid or firm bodies in places of contact of...
If amalgamny UV of a lamp accidentally break, there is no need to make action for a demerkurizatsiya, rather accurately to collect amalgam and to send it on utilization as a regular luminescent lamp.
In advance I apologize if it a little off the point, but it was always interesting to me why ultraviolet lamps are more expensive at 5-10 time regular :)
UV lamps have capacity from 100 to 800 W, in...
Hello! Sorry for my English. Walking down the street and saw a rare shot for our country (CIS, Ukraine) :) The sun has done its job + savings.