Type: Posts; User: Dann Prentiss
Yes. Every body has given me some great input. Thanks Tech83. Thanks everybody
The indoor coil is new and the txv is new
Yes It is
Yes Valves are open
The only thing I have not checked and I feel like an ******* now was if it did have a screen. I have scheduled to go back to the job Wednesday with new txv valve and will definitely check to see if...
Yes I understand that completely.
Yes The system is defiantly under charged.
I can not get a super heat because I cant get system fully charged to take one
No Txv only
No can't get a full sight glass. High side goes to 250 and it says the pressure in system should not exceed 300. Filter dry seam very cool. But compressor heats up quit a bit. To hot to touch.
Yes I do Thanks
Thanks guys. Never had an issue like this before. Never do favors for people
Thanks man. Will the compressor re set it self?
Oh ya What is id wager?
I have pumped system down several time. Pumped nitrogen through system. Should I remove filter dryer? Will the compressor reset it self do you know?
A/C evaporator coil. Sorry
It is a hydro air handler coil Advanced Distributor Products (ADP)
I have my own small company and I know I shouldn't have done this but I'm kinda stuck now. I have a carrier condensing unit Model 38TRA060330 R-22 and bought a ADP 13 seer, changed out txv vale to...
Am I allowed to ask Questions here?
I'm new to this site. Not sure if I am doing the right thing here
Have a weil mclain boiler with no tags. Can I find a serial # on block? Trying to find the age of it.:anyone: