Type: Posts; User: lee107
Search: Search took 0.00 seconds.
Subcooling with TXV should be 8-10 unless otherwise stated on equipment as design pressure ___ subcool. The amp reading could be anything since he did not know how to adjust refrigerant level...
This is the Ask Our Pro's forum. In order to post a response here, you must have verified qualifications and have been approved by the AOP Committee. You may ask a question by starting a new thread....
08-30-2012, 07:11 PM
We would like to go down for a couple of months and help established companies with there excess work. We have NC CFC cards for handling refrigerant but do not know if that will work in other...
Results 1 to 3 of 3