Type: Posts; User: d_d_c_jci
Search took 0.00 seconds.
The architect and customer preferred this wiring
scenerio because it is a datacenter if NCM or DX
goes down they want local control.
The first thing I thought was the AI to AO scenerio
Check your email for further instructions.
When you run that patch it will upgrade you
from 8.07 to 8.08B. You do not need anything else.
Check your email.......
Have 2 fans and 2 DX-9100 controllers.
The fans go to a common duct.
They have separate discharge sensors.
If I installed a 4-20ma discharge sensor
in common duct, can I wire it to both DX-9100?...
Usually on the blue screen, you single click on the system
that the processes have been programmed for (AHU1, 1stfloor,etc)
It depends where they created the processes in Metasys.
, then on bar on...
The only thing I know of for DX power failures is below:
Is there a program for DX power failures?
See the Pwrfail.exe and Reset.exe files located in the DX-9100 Tools...
Have you tried to connect with hyperterminal?
Sounds like GPL is using an Analog Data point to write
the setpoint in CS object.
Go to processes in Metasys and see if there is a process called
setpoints or something like that.
If GPL files...
OK...but what about from the server.
I cannot look or modify the program from
the server if it wasn't in Visuallogic?
I have a school district with Envision for Bactalk on a server.
Each school has at least 1 TUX, ETH, etc.
The field controllers vary because they were installed
when they had IBEX.
I know I can...
Thanks again for your responses....
I will get pricing tomorrow on MP580
Can it be programmed through a Summit workstation?
I have Lonmaker but if I can use the workstation
it would be better.
Only Comm3, Comm4, and Comm5 on BCU.
MP581 might be too much.
This is the reason why I thought UPCM and now
you guys just reinforced my thoughts.
What Trane controller is best for turning boilers
on-off and controlling secondary valve?
Would it be UPCM?
We have Trane Summit BCU with workstation.
How do I find / modify the IP address for Summit?
Has anyone tried to bring the N31 into Tracer Summit
How hard is it?
Is there a point limit?
Your HVACPRO settings are fine.
You need to change your jumper on your actuator to
reverse-acting. But make sure when you lose
power to the actuator it spring returns open.
NAE and NCE are different controllers so THERE IS NOT a NAE25.
There is no NAE25, only 35,45, and 55.
Anyways, there is no simple way to reset passwords
without blowing the database away. (N.U.T. the NAE)
Then reloading it.
Are you sure you typed in the...
Yeah, but the problem is when maintenance turns the
univent off to change filters the command from the n30
goes away and defaults to summer until the master is toggled.
Have some univents with UNTs
that has sum-win binary input
I am using the N30 master sum-win
to override these inputs.
When univents lose power and come back
on, they default to summer because...
Does anyone have RTU, MAU, and VAV w/electric heat
graphics that they can share?
Either standard or advanced.
Has anyone tried to integrate into a Dectron
unit that has a Siemens OP393 III PLC controller?
Anyone know what the controller's protocol is?
You have mail......
I found it and I cannot attach, what is your email?
You should be able to get the fieldserver already programmed.
I do have a .csv file but I have to look for it.
It is Ingersol modbus to N2 I believe so I don't know
if it will help.
Does anyone know or have an example of
a sideloop that uses an input (fan status)
to turn the PID state to OFF or control?
Also, using summer /winter status to change output
from Direct Acting...
I think the issue was it was performing a recalibrate
at the same time mourning warmup was active and
therefore overheating classrooms.
I set the schedule for 2:00am to 2:15am.
Been like this for...
First, check to see if the jumpers on the back
of the DX-9100 are correct.
Check the program to see if defined and ranges are correct.
one blue and one orange on 15vdc terminal of...
Sorry, I just seen where you stated The circ. pump is
running and there is proof of run status but you have a
no flow alarm. Do you have a point that states the
pump status is ON, well what...
From what I am told...
No...it is Siemens software that you can add
a BACNET driver to integrate to a BACNET system.
Can you email that to me too:
Thank you in advance.
Did you try to email me that UPCM edit manual yet?
Thank you in advance.
Thanks for the reponses.
I will put the schedule for 5 mins
in unoccupied mode.
I also seen some of these boxes stuck in recalibrate mode
during the 5-5 schedule. I had to change it back to...
I have separate bldgs with Metasys PMI.
The customer wants to put it on their T1
but wants us to supply a firewall.
I am currently looking at Cisco.
What firewall do you recommend?
Is the recalibrate for the damper only?
Should it be setup for after hrs or during the occupied time?
Does anyone know what the Trane Summit is
doing when there is a 5am to 5 pm schedule
for VAV recalibrate. How do I verify that all boxes
Tnaks but I already figured it out.
It was my USB bluetooth adapter.
I had to buy a D-LINK adapter instead
of the one that I had.
I don't know why it didn't go through but
I have no manual but if you have one can you email it to me?
I went in and I copied someone elses password to create my own but
didn't pay attention to what I hads access to.
I will check again.
It is controlling an multizone airhandler.
I'm am trying to find zone setpts and cold deck setpts
Trane is coming in a month
There are no as-builts and the customer has to wait a month
for Trane service. There is a link on Summit to PCM edit but
not UPCM edit.
I did what mallron said and found only the OA min pos setpt...
They are at version 16.
All i'm trying to do is add the point to the graphic
so the customer can adjust.
I will check the wiring harnesses and wires tomorrow... Thanks.
By the way I'm trying to find the controlling setpt...
room setpt or discharge setpt.