Type: Posts; User: mrbean
you could try to meg your motor see what you get
ohm furnace and its components disconnect power to it first
well i guess will never find out what the problem was
spider web in your orifice ?
make sure tonnage of con unit much air flow of air handler
try Chinese if you please
use Skype to see what is going on
if you look closely rotation is ccw only
What country ?
and your point is?
see if you got power going to ventor motor
Can you please send one to me
let it equalize
r22 contaminated with 410
what will happen if you mix r22 with 410
system 28 lbs r22 add it 1 lbs 410
any dogs around?
i have been using dewalt for 4 years now and it's going strong
i think its for heat pumps
that is correct
it's time for new furnace for surre
double your cost
Ok you lost Me rundawg
replacing old lennox
can anyone tell me how do i find cooling capacity of the old unit
need it to know if anyone pays attention
i dont like them
minimum line length only for ductless systems LG 50' and so on