Type: Posts; User: nyrfan
Search took 0.02 seconds.
Actually my unit was installed with a standard blue fibergless filter, nothing pleated.
I guess if I was to go by everyones advice I should just stick with them.
Does anybody know a place to shop on line for return air grills? I would like to change mine to have the filter at the return as opposed to in the A/H.
As some of you know I recently got a new XL15I with var. speed air handler.
My question is, if I am going to change the filter every 30 days and I would like good efficiency but more importantly a...
Wanted to give a quick update, as I know some of you were interested in my decision.
The unit has been wonderful so far.
Temps in Orlando have been in the low 90ís for the most part with...
See other post!
[Edited by nyrfan on 05-22-2006 at 09:16 AM]
The house is just about 9 years old. The house is ranch style 60 ft long by 40 ft with vaulted ceilings so I cannot access all of the ductwork as I have no idea how to get to the back of my house. ...
Should me vents be completely quite? Right now with everything in my house beside the a/c I can only slightly hear air from the vents, I really have to listen to notice it. Even when...
I do have a question.
What would be some of the signs that my current ductwork could be undersized for my new 3.5 ton unit?
I am the one who had so much trouble deciding on which direction to go; the choices are just mind numbing.
In the end as you can see I went with the 3.5-ton xl15i, reason being I...
They installed the Trane TC803 with the humistat, which I have set at 45%. Looks excatly like the visionpro!
As for the whole house filter system, my wife wanted the new Trane effects but 1-they...
The noise I hear is not much more a faint air sound and that's only on the rare occasion that the fan goes into high mode. I'm sure there is a bit of more ressistance on the...
It's a VS air handler and I can assure you the fan blows at different speeds which and from what I understand is supposed.
As for it cycling, it may be oversized but it's keeping the...
Well I bit the bullet and had the 3.5-ton 15i installed on Saturday. I know I said I was going with the 3 ton (16i or 19i) but I just believed it was too small.
Anyway the system seems to be...
3-Yes variable spped handler
Yes I am get the Trane TC803 with a humistat that will contro the handler speed.
Yes the problem room is the farthest but 1 it's the biggest room in the house and 2 the...
It's not that I want the 3 ton more or less then the 3.5 ton, I just want what it going to keep me cool. Unfortunately everybody definition of cool is different and mine is quite off the chart.
This is just driving me nuts. No matter which way I go I'm going to wonder if I did the right thing.
Anyway I made the decision to go with the 3 ton 19i and have the return opened to 24x20. I...
"noisy" is hard to difine. I think it's pretty noisy but that just me.
It was built in 1999 by American Heritage.
Lets assume I go with the 16i and have the return cut to 24x20. Do you think...
Wow, I have a 3 ton now and it's 18x20.
So overall you think I sould go with the 3ton. Would you suggest the 19i or the 16i?
Also even though I am going form a 3ton to a 3 ton do you think I...
OK according to the contractor, he claims this will increase the cfm (something like that) by 200 and with the amount if grills I have, the very staight runs, and the by increasing the return grill...
I'll get that information and post it in an hour or two.
The only thing I know right know is the rerurn grill if I go with the 3.5 will be expanded to 24x20.
Can an extra 3000btu's...
According to both contractors the duct system is fine (They did not use the words undersized, they said big enough for a 3.5 ton if I go that route) 1 contrator said I had r30 up there, the...
Here are the 3 choices:
Air handler: TWE040E13F
15i 2TWX5042A rate at 40,000 BTU, 15.35 SEER
19i 2TWZ9036B rate at 37,000 BTU, 17.60 SEER
Air Handler: 4TEE3F40A
Yesterday when I got how my exact readings were:
Temp set to 77
Actual temp 79
Outside temp 92, 31% humidity
Temp set to 77
OK here we go:
I called both companies and asked for the ManualJ:
Company 1- No heat load done.
Company 2- Calculation of 43009, 9102 of that is latent heat
Company 3- Calculation of 42601,...
Sorry fixitmanmc but your post it a bit to tech for me.
In the end what unit would you recommened?
Right now I think I've narrowed it to the 16 or 19i and will Solar screen my huge South and...