Type: Posts; User: VAV616
Search took 0.01 seconds.
Id agree you could probably use a good evaporator cleaning.
aside from just running the chemical(hoshi is Stainless Steel) through the clean cycle for 45 min or so you should also unhook the...
And All the BUGS you got hanging around a whole Cord of wood in your yard!
Id just hate to see somebody spend a whole lot of money, and then on a hotter-than-usual summer the guy is calling me because it wont keep up, or to him it seems like its not cool enough, or some...
they taught us manual J, D, and P, but id never seen S until now,
you guys already know the right way to do it is to use manual J - it makes a big difference what kind of insulation, windows, and the angle the sun hits your specific sized overhangs that shade the...
the whole time I didnt suspect it because i knew i had changed it just last year.
turns out, after checking my records, I changed that sept 1, 2009, almost 2 years ago. ...
i did change the water filter, clean the condenser and use cleaner on the water circuit when i first did this one.
so im pretty sure thee only problems left are the water valve, and this evap...
k, the amount of water that should be frozen by the time the
float comes down should be the same, I agree and ive been thinking
that same thing.
so then why is it still dropping less even...
the charge seems right on now, 10 degrees subcool
superheat still hunts a little but no drastic swings.
it supposed to drop about 13 pounds, i didnt weigh
the batch since i redid it, its making...
you know I called several places and nobody had an HH smaller
than a 163 for the liquid side.
so i put a regular 052 on the liquid and an 164SHH on the suction
still dont quite have all the...
it annoys me when people wont spend the extra $200 some-odd bucks
to get a new Fused disconnect.
what you barely see is the #10 green wire reaching over to connect to the frame of the...
Well if you gowith the original maufacture you may still need
An adapter curb. But it will be less drastic
i found this for sporlan driers
APPLICATIONS A special HH core
Catch-All Filter Drier is available...
yes i mean the evap temp is 0 degrees. so the superheat is floating between about 10 and 30 degrees, with the sharp drop-off back to 10 then slowly working its way back up.
what do you mean by...
old r22 ref cuber.
the water system is working fine, about 30 min cycles, but its only dropping about 60% as much weight as it should be.
110 cond temp, 10 degrees subcooling - evap...
oddly I think hot-shot is More expensive than 134a.
was the filter/dryer one of those copper bullet style ones?
I have been told they have small desiccant bee-bee's inside
that may actually...
your gonna get out the torch and Braze on the gas line?
to me the more important part is that copper is bendable so all it takes is somebody to accidentally smack...
ya, vacuum leak test : | and i've had somebody else try to tell me that formula 409 was the best leak detector in the world lol. vicegrips ha - i hate to use flare couplings anyway. I wonder...
i have to admit ive done that before - but mine had a service port installed :p
It was for my brother and he didnt have the money to pay me anyway so I wasnt going to go and buy(or spend the time to...
we visited the new hockey rink where i live, It was an ammonia system with a brine secondary. the brine ran in a sand base under the floor, idk how big the pipes where or how close they are though.
Im gonna say this was most definitely done long after the original inspection when it was built, either by the home owner, or some "contractor."
To me it is just downright dangerous even if the...
my all time favorite -
first pic you are looking at two capacitors, a contactor, and the wad of duck tape that was used to hold it together in a ball and set inside the unit.
this is a...
sadly I see this all the time
the original was a York, if they'd of got another York, or at least something that sat the same direction it would've been ok. but the Carrier sits sideways on the old footprint. and for me, the...
dont you hate it when you loose a job to somebody else, then you come back to see some crap like this : /
and it doesnt keep up above 95 degrees,
and that is the filter access side of the...