Type: Posts; User: paulturnkey
could I get some info also thanks
I,ve seen 277 single phase which would be one leg and neutral of 480 3 phase don't recall any 480 single phase
sounds like system is well over charged check l.l sub cooling to verify
Call Turn-Key Engineering 978 251 8001 We are looking for help.We are located in N.Chelmsford and work all over eastern ma.,southern nh (no residential or refrigeration) all com. hvac service work.