Type: Posts; User: sr20detb13
Search: Search took 0.00 seconds.
thanks a lot guys
well can anyone help me out with a forsure? is the head pressure less due to the way the unit works? do you usually only check suction?
partially gas and liquid, thats what i was reading. thats why i didnt want to follow the text book pressure data. im not sure with these new systems.
Ok this is my first real post on this forum. i am certified in 410, but havnt been in the field for awhile. This is a super new 40,000 btu mini split, with dc inverter. So heres the run down. leak...
06-19-2008, 04:05 PM
this sanyo is pre charged with 7.9lbs and is good for 10-100 feet line set. just needed to leak check, vac lines, and test run. And runs awesome.
06-19-2008, 02:49 PM
yea i found this out last night... the line is sitting with freon in it, with not enough insulation and its just getting cold..
06-19-2008, 01:12 AM
I'm in the middle of my first ductless mini split install, so i took some temps in test mode and in full cool. temps seemed alright but I did noticed that after the system was just running the fan on...
Results 1 to 7 of 7