Type: Posts; User: Toolpusher
Search took 0.02 seconds.
i'd be intereseted in talking with someone. I'm self employed in Ohio. have been for over 8yrs. went to ITT Tech for HVAC training in 1990 . Relocating is no big deal. but the company has to be...
currently self employed in a town about 45 miles west of columbus. I dont have a degree for the work you listed but, i could it. or relocate for another position if something comes up. Just about...
i was in johnstaone supply this week, by the cashier office they had an ad by envirotemp looking for help
I have had 2 units in an attic.
1st one I used Ductboard to make a box for the condensate pump to sit in.
And wrapped the tube from there with foil back insulation.
The second I had a 1" pvc line...
I checked on the cost and operations difference between the 15 & 18
I'll save the cost difference in 3 yrs of operations.
Go with the Variable speed drive air handler
It's a closed system.
the refrigerant doesn't know or care what direction it's going.
It has to change state in 2 locations.
As long as the charge is correct it will change at those locactions,...
Some of the water coils wood heaters around here have been installed in the return air,
I have had to move the ones I have seen do to the hot coils tripping limit switchs in the furnace.
On the out door circuit board there is a pin for the defrost cycle timing.
Below those setting is a pin for compressor cycling.
On the XP-15 that pin needs to be in place,
On the XP-13 that pin...
I know Lennox will run the H/P in heat for 1st stage but it has a sensor that will switch to 2 nd stage at a given outdoor temp.
And I think that temp is around 45*,
so they don't get much...
I used to wear those long dish gloves.
But now I wear those rubber doctor gloves.
I have a 1 gal plastic ice cream container that I keep old oil filters and gloves in. Keep the lid on the tube...
Why would they install the coil that direction ?
isn't the other end supposed to be on the furnce.
That could be why the gap is present.
The opening is away from the blower so the air is hitting...
BINGO,,,,, That matched VS air handler will have the correct TXV already installed. If it's a H/P it will need a few minor wire changes made inside the indoor unit as well.
Thanks for all the info guy's.
More neah's then yeah's says alot. To much to ignore, in fact.
I'll have to let this one slide it seems.
My area is very Very limited on employment.
We have lost 4 factory's in 8 months
School levys continue to fail.
People here aren't buying units, cutting back on maintaining equipment.
you sound like you have been burned once or twice
West central Ohio,,,,,,Go Bucks.
17 yrs in the field.
alittle of everything,
started at the bottom installing resd.
to 30 ton comm. units
self employed for a time .
Now just trying to...
My original question is to see how other large outfits allow for stock.
I'm not worried about the equipment out there.
I thought it sounds odd to send a truck 2hrs out of town with little to...
Would think you would have to pick up extras along the way.
On the basics at least.
Contactors, capacitors, transformers, relays. motors, fuses.
I just can't see running a truck without stock....
Would be home every day.
They say to give me an automatic 40 hrs would mean I'm salary.
So they say 38.
Just seems like alot of waisted time. I want to fix what I find wrong , when I find it....
I'm looking at joining a service company that is nation wide.
From what I was told by another guy who looked into this outfit, They don't have much or any truck stock.
They don't have company...
rule of thumb is not good.
Some thumbs are different from others
So which should I go with ?
Haven't you been reading the responses.
If your worried about the $400 more then cut back on a couple outlets .
Lennox has been the direction you been given, listen...
Just adding some input,
In your area, if you go with 2stg H/P.
It will run most of the winter in 2nd stage anyway.
You'll get your 2 stage operation best in the A/C mode.
So is it worth...
Leave unit as it is.
Set new unit on top of it,
cut lineset repipe to new unit. Same with electric.
now it's where you can work on it in the future.
Til the brick layer adds to...
The match up is more critical with the coils in the heatpump set up.
some heatpumps require a slightly bigger indoor coil during the heat mode, when going with R410a.
But still a good point to...