Type: Posts; User: Bordo11
Search took 0.01 seconds.
21degrees, thanks for advise, I will make sure it is rev. 14.
Wanted to remove without breaking the old one just to know how to do that in case, as DanW13 mentioned, will need to paint the wall or...
21degrees, after a few sets of massages on the thermostat body it still did not open and almost ready to be pull of the wall. I will need to use a screw driver. Thanks for encouraging advise :p
Does any one know any specific way to remove Carrier Infinity Control?
Rocking up/down until interlocking tabs release stated in the manual does not help. Is it any specific points on the case to...
Thanks for your suggestions.
I wanted to make it simpler, just making an empirical assumption.
If the system would lack returns by opening an air filter compartment and creating additional virtual...
Using Infinity 58MVB60 air handler installed the static pressure showed by Infinity thermostat display is 0.9 1.0. It seems a bit high.
The air duct (supplies) sizes I have calculated for the 600...
The call to a local municipal office did not help.
Does any one know what are the local codes for Illinois, Chicago area?
Is a solid core (instead of cellular core) PVC 2 inch diameter...
I do not know how to get them, oops:confused:
But again, the good thing is that the high-pitched noise is less bothersome comparing to reciprocating compressor lower-pitched noise when it goes through the walls and windows. Inside the house the...
It is already a month, my Infinity system is up and running.
The duct work installation took eight days for the two people team.
The pictures will follow later. :p
The humidity control and...
Dash, tpa-fl and all of you who helped me, thanks a lot.
I have already placed an order for 24ANA136, CAPMP3617ACA coil and the rest of Infinity system components.
Will see how it looks after an...
Dash, maybe you know from your experience which unit is lauder 24ANA1 or 24ANA7?
You have installed already tons of those systems, you should know.
I want to make my pick and order the system...
The table for 3T ANA7 at 2 kHz (ear is sensitive for this rang) shows a higher noise by 6dB on the high stage.
The humming noise at 125Hz is also higher by 7 - 8 dB.
I guess on the 60Hz the...
So, what is the reason to use a scroll compressor if the main noise comming from the fan blower?
Is it really ANA1 is twice laudier? The dB sometimes do not show the real subjective noise. In other...
Aircooled, thanks for your support, holding a hand and walking me through the fire.
Just last unknown thing has left - coil selection. Still do not know what P/N to choose.:confused:
OK, I have finally settled.:D
Thank you for your advices.
Final solution, I will be going with 2-stage Infinity 24ANA136 A/C and 58MVB060-14 furnace.
ANA1 has a two speed blower fan and the...
Dash, why coil CAPMP3617 will not fit with 58MVB060-14 furnace, as you have mentioned?
Can you advise please what would be the right matching coil for the horizontal blow application (installing in...
It looks like too much mystery and controversy in the price politic on the IQ Drive unit.
At least what I am experiencing wit the dealers in my area.
I want to call to Nordyne ask which dealer they...
I have already spoken with one Nordyne Maytag authorized dealer.
For 3T A/C, 60kBTU furnace, matching coil and thermostat (whole package including installation) he came up with the price that is...
Let me say thanks to all of you.
This system looks very intrigue. Now I need to do my own homework finding more specs.
The only doubt I have left (tpa-fl has mentioned that also) is the humidity...
Kuryakin, I am really appreciated for your advice. I will meet tomorrow with the Maytag dealer. He promised to get the data sheets with the electrical and noise data.
The bad part is that he does...
Is it possible to get the data sheet on the IQ Drive series system, specifying the noise levels, min and max cooling capacity and etc.
It looks like the quietest system on the market, songs...
Thanks to all for your ideas.
I was surprised that none of the three dealers were doing a manual J calculation during the HVAC estimation in my house. This is why I have decided to do that by my...
Dash, thanks, now I am getting closer to my final decision.:D
The last thing bothers me is the system size (cooling wise) selection.
I have done a heat gain calculation with HVAC – Calc, using...
Dash, thanks for clearing things up.:cool:
Novakht, I have thought about this model, but I need a horizontal unit for my crawl space. 58UVB comes only as a vertical.
It was a day when I was...
I will rephrase.
My load calc. shows 30,200 total heat gain.
Is it a good sizing approach to choose a 36,000 BTUH A/C equipment (25,800 on the first stage) if my load calc. show lower?
Dash, thanks for your reply.
I just want to add, it will be a new installation, currently I have a window unit. The furnace unit will be in crawl space. All ductwork will be new, any sizes might be...
Installing central A/C in my 60s house.
I am not worry about the heat loss; my house has a radiant heating system.
The furnace heating capabilities would be just to speed up the heating process in...