Type: Posts; User: Merkas
Search: Search took 0.01 seconds.
Try here for manualhttps://www.hqs.sbt.siemens.com/gip/general/dlc/data/assets/us/APOGEE-Heat-Pump-Controller---Multi-Stage-Owner-s-Manual_A6V10308419_us-en.pdf
Well I figured I'd do a follow up. So I've managed to us the ICC xltr-1000 to pull the BACnet points from a Carrier 30MPW system (after the Carrier rep put in the CCN to BACnet card) and export them...
Have a customer that wants to use an ICC xltr-1000 to bring a Carrier chiller BACnet MSTP points into a Siemens FLN. I looked over the manuals and it's kind of vague on the Siemens FLN side. Sounds...
Monitor "your own node"
APOGEE Powers Process Control Language (PPCL) Userís Manual
This resident point indicates the condition of communications.
Depending on the...
02-28-2013, 05:16 PM
Ok don't laugh too much at this.
1) Go into report builder and create a new Trend Definition Report. Click the Add button and in the object selector window enter * as the point name and do a find...
I know, Just checking that gazoo knows that. Should be able to do it from the front end even if its never had telnet enabled before. I do it all the time.
Is this PXCM on a PII hard wired trunk or on ethernet?
Is there an Insight front end? Go to system profile and double click on the panel you want to enable telnet. Find the button "Terminal Definitions" a config window will open with a check box to...
"You all agree/disagree using two different BACnet netowrk numbers on the same network is going to cause trouble like this?"
Not sure? Anyone?
Can you move you "BACnet/IP 47808" port to another...
Formulas for a 4-20mA input on a UC
Slope = (V2 - V1) / 2602
Intercept = V1 - (Slope x 650)
V1 = 0
V2 = 65
Slope = (65 - 0) / 2602
Slope = 0.024981
From the Book table B-3;
Range Slope Intercept
0 - 100 0.038435 -25.0
Can you log into the panel from the HMI port and poll the rev string. Or from the front end in system profile. If it is a rev 3.0 , 3.1 , 3.2 your true BACnet. Anything in the 2.X range is P2.
If "Siemens panel that already has the BACnet drivers" means it is a P2 controlled loaded with the BACnet MSTP driver then your out of luck. Siemens has to manually build the application and loaded...
There is no option for UC in point editor. Your 1000 ohm RTD would have a slope of 0.1 and intercept of -40.0, not taking into account wire size or lenght.
Check out Appendix B. Slopes and Intercepts of this manual
You can change the slope and intercept for the UC from the edit points menu. See the attached. highlight the field and start typing your values in. There is no calculator built in for this....
00010 PT1 =(6.112 * 10 .ROOT. (1/(7.5 * DEGC /(237.7 + DEGC))) * HUM / 100)
00020 HUMIDEX = DEGC + 5/9 * (PT1 - 10)
To raise a number to the power of another you use the...
You need to delete the printer from System Profile. Also there is an Insight Printer Service that needs to be disable and stopped. Once those are done you're all set.
Realy that simple. The virtual point doesn't even realy need to be created. IE:
PPCL in panel 2 could be: IF ("TEST1" .EQ. ON) THEN ON("TEST2") ELSE...
Ethernet or RS-485 (P2)? The setup is different based on the communication type. Do you have a PC with a serial port and the MMI cable to connect to the panel?
Do you have full access? In other works do you have config/edit to program editor and all access groups. You can check in the user accounts application. If so then you can upload the panel databases...
10-18-2011, 10:13 PM
you've got mail
Had this same request from a customer just a while ago. If you don't need user interaction and just want a slide by slide display of dynamic graphics I used a free app called AutoHotKey...
I was an electrician by trade before I became a Service Automation Tech (non Union). With that said, on small service install jobs I'll install the controls, wire, program and build graphics. On...
Results 1 to 25 of 31