Type: Posts; User: mpatrick
Search took 0.01 seconds.
I'm sure they will take care of you guys just as well as JCI took care of the York controls guys. :cliff:
[Edited by mpatrick on 08-11-2004 at 11:47 PM]
Changed the coil today.
16 degrees across coil
11 degrees superheat (of course TXV)
12 degrees subcooling
Evap pressure 72
High side 225
I will post complete results next week when I...
No plans to discontinue the DX9100.
Goober is correct, you need GX9100 to program.
I have decided to replace the evaporator coil. I will be installing a new coil with a TXV this weekend.
Before anyone asks:
1. I have CFC universal certification (got it years ago)
2. I will...
I have managed to lower the KWH usage to 80/day, by doing the following:
1- Run pool pump early in the morning so the pool is clean when the wife and kids get in. I found that they were manually...
Just to calibrate what I mean by high electric bills.
$543 last month for a 2700 sq ft house in Houston. Rate is 11.1/kwh, usage is average of 145kwh per day. Other large loads have like the...
Conventional split system (not a heatpump)
Rheem Model RALB042JAZ
Blower filter and coil clean, blower door closed.
Cleaned condensor, not perfect but reasonably clean.
Expert opinions please:
I have low performance and high electric bills. Moved in to the house 4 months ago.
3.5 Ton system 11 SEER Rheem (7 years old)
Horizontal A coil
Outdoor Ambient 78 DB...