Type: Posts; User: lontshooter
Search took 0.03 seconds.
One of the things with the shell command in Hyper terminal is you need to have the proper settings to connect to the shell, those settings are:
Bits per Second: 115200
Data Bits: 8...
IF you could give a little info on the system, I would be able to help you out.
Is there a time schedule or is it a ATS attached to a point in the system?
What is the main...
Been busy and not alot of time to get here, but here it what you are encountering with those inputs.
They are ave inputs, but they scan only a small number of inputs on the ave then...
My position is that you can use any good open protocol you want.... or you can use Lon or Bacnet. Doesn't matter to me because in this changing world you will now have to work with both....
The easy way to clear the device and redownload the sav file to it is to use the red button on the board to reset the controller and power it down and power it back.
Reload sav file for...
I am intrested in the MR88R-C, shoot me an email in my profile.
I am with you on this one also. I had to replace a E3 with a SS2.0.
I ran into the same issue that you are having.
Make sure that you have the CS4 release of contribute to work with, you...
The big splash will be at ASHARE in Las Vegas for the software which will be name StructuredWare on the Wonderware platform.
Lots of engineering time is going into this product to make sure the...
Have you tried leaving the username and password blank and just hit enter.
Then the next would be username: admin and password: leave blank
Then the other one is username: user...
You have mail.
Is there a limit to length of Lon wire ran from stat to stat?
Go to this link and look at page 36 & 37, but I would read the whole document as it will help you out.
I have had one issue with that stat and about the same issue that your are having now.
First thing that I would be looking at is the stat and if the XIF file is loaded into the stat...
You've got mail
You've got mail
Any programing or control of an Invensys/TAC system is done thru Workplace Pro and Workplace Tech.
There are two sides to Invensys/TAC, one is the LON side and the next is BACnet.
First question are you using a router or switch that your computer and the LIP are connect too, or are you connected directly to the LIP from your computer?
The default IP address for the LIP is...
Crestron uses what they call Crestronet for there commnication format.
They will not talk directly to any device other than a Fieldserver device.
They have agreement with Fieldserver to produce...
What are you looking to Integrate with Crestron.
Have done a few projects with there systems.
Most common communication is either RS-232 or a LAN connection, but there are...
This should help you out to resolve your issue with the controller.
Need to remember that you can not retrieve the code using the new GFX programming software.
You need to use the...
Couple of question for you to allow for more help.
How long is the run for the main trunk line from computer to farest device?
Are there already repeaters in the line for the...
Do you have a copy of the SAV file that you can email to me and will look at it.
Well I have heard the rumors running around my area also.
The Delta guys out here have been told to keep a lid on everything and not talk about JCI and Delta.
If JCI buys Delta, it will give...
There is a file installed with some of the newer programs for checking you licensing status, that is called FNP Licensing Service.
It is common to Adobe software.
It was design to check the status...
You need to get the software Workplace tech by TAC version 4.0 and better, to be able to due balancing on the Micronet controllers.
The software is properiatary to TAC(oops!!!!) Schneider...
SNVT_time_stamp#LO: text(date(year, month, day), (" "), time(hour,
It is how the time stamp is defined see above.
This would be from a controller that you want to...