Type: Posts; User: Fmech
Search took 0.01 seconds.
have customer with no access to system
engineer left and took/changed password on his way out
can anyone point me towards a work around or security file extension ??
Getting an occasional fault per the engineer
have not seen his machine yet to check logs. going there monday
oil levels are good and temps are at 138 degrees
Thanx for the quick response.
would anyone have an e-mailable copy of that software out there???
and do I need an interface or just cable direct hook up. I have the parallel
to serial patch...
Have a job with a problem PCM I need to upload the program and load into a new PCM board. I already have trane tarcer Rover version but I am pretty sure its not capable of loading a PCM. Can...
I have a front end computer there that hasn't been in use for ???? who knows
what would be the suffix for the b/u file??
the front end does have the graphics how ever tried a serial cables hook...
Actually, I have both a copy pf the software (ibex for windows) and the parallel port "key"
More specifically, i was looking for some assistance as to what my laptop hook up would be....
perhaps I don't have the exact correct name for this module
Its a wall mounted back lit LCD display module with up down left right and N & P keys for navigating around to the individual VLC's that...
Could I also trouble you for the same info
I have a alerton microset that lost its program and am looking to scan the buss and reload the points
Most software has the ability to upload and copy an existing program set up out of an existing controller and then down load it to another controller on the network.
is there a carrier publication...
have several jobsites that I need to replace VAV box controllers &/or reprogram
337cfan & VAV controllers. Can this be done through the comfortview front end
on the network?? or do I have to...
[QUOTE=HVACRACbob;7352592]230.10-m1 (804) ???????
Is this top secret???????
Out of 100+ People Begging]
After your tirade can we assume that you would like a copy of that form
you just might want to redo your email address in your profile, It's wrong
yes, I resent it to your correct email address
After a LOT of calling around FINALLY got the info I needed.
To any and all who may have followed this thread the following is the answer.
For the millenium recip chiller control.
Still having a hard time getting to the bottom of where the machine gets the correct amp rating for the over current parameter on this YCAR chiller.
If any of you readers have any thoughts. After...
he chiller had been running okay (to my knowledge)
the building engineer had gone up to reset the unit after a bad storm
and apparently left the access door loose and got some (or all) of the...
The dip switch settings match. the current draw (combining both wires for each phase is 71 + 72 = 143 though only one wire from each phase goes through the current sensor and one does not, as I...
its a split feed 2 wires per leg one each goes through the klixon and one does not
I measured the 3 (separately) that go through and the three that don't
I have a YCAR0230sc46P aadb SN RBKM6505AA
unit is locking out on over current high amps reading of 160% @ 164 amps. The problem is that I'm reading 71 amps actual on all six feeders to compressor...
Just a FYI Update>
Went to this job today and the board is slowly fading into the sunset.
I now have no access other than status, but, the good news is that when i was there yesterday I was able...
thanx for the response...
before I get back over there when I hit program does it normally prompt for
for that password (cause this display currently does not) or when "program" is on the...
York Semi Hermetic YCAJ 0140 I can't change the full load amp settings The chiller starts and runs on both circuits but the chiller locks out on high current . when I hit the current button it...
I need someone in Johnson land for this. I have a m-3 Graphics GDF display
I want to add a button to basically execute minspecter and then open up the schedule file for that piece of equipment...
just saw that you have this 230.10.m1 info I was looking for
could I possibly trouble to send it to one more guy?? My email is Removed
I have a ycas 160 that we put in a new compressor 2 years ago...