Type: Posts; User: ttolve
Search: Search took 0.02 seconds.
06-07-2005, 11:21 PM
Accumulator reciver? when did they become one of the same?
Mutt and Jeff will be screwed if so poor bast#$^% gets hurt.
06-07-2005, 11:16 PM
Oh by the way, does this er umm thingie have a er um a evap coil?? and could it er um a maybe leak? er um a well and you know just a thought. Guys I thunk we're...
Rules are rules no DIYers.
I don't cook great meals... I'm not a chef!
I don't arrest people.... I'm not a cop!
I don't know how to cure... I'm not a Doctor!
Are you getting this!
With plenty of...
Dont be offended, but did you send these pictures to the POPE! it would explain his recent illness.
only you get these jobs. I really feel sorry for you.
That said, good luck!
03-27-2005, 02:22 PM
Suprized payson dident get this job! Just kidding.
"TO ERR IS HUMAN< TO REALLY SCREW THINGS UP TAKES A EN GA NEER"! Always keep Y and W and G shorted at the TB board untill all construction is done!...
03-26-2005, 12:54 PM
Is that a T.V. antena on the roof? where is this place?
please tell me not In the U.S. That guy can't be a contractor, he looks like a misplaced Juan Valdez ( coffee bean guy) I said it once I'll...
sinder blocks for base? I don't know that I would use those!
Ten bucks say's the guy from Hell country gets to work on it! I can't wait for the pictures!
Copper Nat. gas lines are bad to begin with.
Think they ought to be outlawed!
Guess this guy really wanted to show us how bad it can really get!
Never saw a nail in galv. pipe
But I have in...
You really pick the job's
you enjoy working in these situations or you get hazard pay
If it is piped to a heat pump it's not heating that's for sure!
Tell me that's not oil under that pad!
otherwise short of the 95-5 joints, no insulation, coil exposed to weather, and one hell of a time to change that drier it look's ok.
Tell me is that oil...
That's not the work of a hack a/c guy!
Look's more like the work of a hack roofing co.
might have removed orig. supports during a repair or re-flash and never took the time to replace them.
getting to the service ports should not be that bad,(located top back side, just below fan enclosure)
It's cleaning that coil! Now theres a challange!
Hey Payson,I don't think i'm local to the area, and it's
not the shot of the Hill in the background that gave away
your position. The place you are has been called by many diffrent names over the...
Blink, Blink, Blink!
Shagged em rotten baby... yea
When you drive things that grunt and eat hay!
When your Contry's primary fuel for heating is wood and coal! Need I say more?
03-04-2005, 11:06 AM
YORK Preditor! copy of a Lennox, I call them York Pretenders. I've got a juck box full of these switches. don't bother with a replacement it will fail as well.
I've had failure after failure. If you...
Results 1 to 19 of 20