Type: Posts; User: harrelson
2 pole contactor used on 3 phase loads = 1 less contact to fail
is the min heat cfm being meet ?
You can enter the CFM you want it will seem like it took but when I go back to look at the setpoints the old value is there
I can change temperature setpoints ok but not the cfm points
I am in...
Anybody have any infomation on the vav4020 and ESS32 pdf?
the job I am working on has the min heat cfm set to high when I use the ESS32 software to access the control I can edit the value but it...
you cannot set up anything in the Ipack with rover, you will see the device when you scan the com link but that is it. if you dont want the heat to operate ever configure the unit as cooling only
so it is misleading when software lets you select the max vdc output voltage up to
ask for refrences
I also dissconected the other AO points nothig is draging the ao point down
thanks for any ideas
I have unt controller that i cannot get the analog out to go over 10.1 vdc
I have it configured for 100%=12.5 vdc the actuator is a mp 5410 and 10vdc will not stroke the actuator all the way. even...
check with your local pipe pipefitter hall and see if they are acepting aplications
is this the olc ccp or the new touch screen ccp
you need to disconect the com link to the tci and try the test mode
do you have a UEM module? if you do dissconect the mod bus and see if problem goes away. let itrun several days you will need to replace the UEM if it works proper with it disconected