Type: Posts; User: JohnLongden
Did you have orange paint on you tennis shoe? Regarding picture 9.
Thanks sarge, I even went as far as switching the wires around since there were extra not in use
I called it in for a supervisor in the a.m. Its just frustrating to leave without a fix
If I'm not mistaken the high legs are off of the breaker to transformer and rest go to sequencer and heating elements. Do you think there maybe a short at the sequencers
I thought about that checked high legs and even checked if elements aren't grounded to the unit. I thought in most cases if there was an issue with high voltage our service disconnect would trip. But...
That's over on amps drawing around 10 respectively. Placed fuse link on 24 volt so I don't have to replace transformer again
Not yet. Checked continuity at low voltage to and from tstat, checked tstat , bypassed sequencer common to fan relay and heat. But still over ping. Help obiwan
Havinf an issue with a sequenced 10 kw heater. Ik now it's pretty elementary, but when energized the transformer blew indicating a short in the low voltage.SOMEWHERE