Type: Posts; User: John Thomas
My take on your problem is a blown dual capacitor. Easy fix.
Have 3 brand new fan control boards for $40.00 each. New, never opened. Will replace Rheem/Ruud, Evcon, and Robertshaw. Please E-mail me if you have any questions. Addy is in my profile.
Brand new TIF XP-1A leak detector. Detects all refrigerants down to .1 oz/yr. Has 7 sensitivity levels to accurately pinpoint leaks. Comes with 3 additional tips. $150.
New driers: Liquid line: 3 ea 052 1/4 flare, 1 ea 082 1/4 flare. Also, 4ea 052 1/4 flare HH sporlan catch all for burn outs. I got these a while back to use with my recovery machine but no...
Anyone play cool quiz today? Did you have three questions? I only had two. Just curious. Thanks
Thanks for the info. I took it from RV and finished in two days, It was great! Was able to talk them down to $200 for 14 hours.
Here in Florida, we have to take Continuning Education credits every two years. Has any one used the Red Vector on-line program? Any comments about them?
Sorry, but if you don't know, you need to get an AC Contractor.
Your reversing valve solenoid is bad.
The symptoms you give lead me to believe that the outdoor unit is not running. I'll bet the unit is a Rheem or Ruud. There's a red reset switch at the bottom of the outdoor unit that you may push to...
Just a test
just a test
Merry Christmas to you, Don, and everyone else on this board. I also want to thank you for the Great HVAC Talk board. It has given me some good info.
John Thomas and Mrs Thomas!!
Tell him Happy Birthday from us. Glad you had a good time.
Thank you and Merry Christmas to you and yours!
[Edited by John Thomas on 11-04-2002 at 07:06 PM]