Type: Posts; User: coldboy
YA, BUT THE STATIC IS GOOD .25
THE STATIC IS .25 AND IT HAS EIGHT DROPS THAT ARE ALL EIGHT INCH DROPS. THE RETURN IS 20X40 INCHES. SUBCOOLING IS 1 DEGREE.
[Edited by coldboy on 03-30-2005 at 06:16 PM]
I HAVE A PROBLUM WITH A NEW 5 TON SYSTEM GOING THROUGH COMPRESSORS DUE TO 29 DEGREE EVAPORATOR. I DID NOT INSTALL IT , JUST TRYING TO CURE PROBLUM. IT HAS A 20X40 RETURN AND PLEUM WITH EIGHT 8in....
There is no big deal in it . I work on anything and fix any brand. I work on swedish and italian all the time If I can"t get the part I subsitute or make it.
I know that trick, From what I am told , it has always had this problum.
[Edited by coldboy on 05-03-2004 at 09:35 AM]
It is heavy frost covering the entire evaporator and the box is kept at 35 degrees. It as two seperate refrigeration systems in it both ar 20,000Btu . One is this R12 system and the other R22. No...
Don't use the condensation pan under the compressor, run the condensation line to a floor drain.
I have a problum with a walk-in cooler with a McQuay RLC-200C-M_11 evaporator and a Tecumseh AgA4534Axa condensing unit and a sporlan Cfe-3-c valve runing 10 degree superheat and 18 degree saturation...
THATS HOW MOST OF THEM SPEEK IN THE SO CALLED BIG EASY!
Can anyone tell me the BTU rating of this high temp comprrssor at a 20 degree evaporator @ 130 condenser temp. ?